Pioneer® Quantum Ultra™ 22,000 BTU 19 SEER2 230V Ceiling Concealed Ducted Mini-Split Air Conditioner Inverter Heat Pump Full Set - No Installation Kit

Summary High Efficiency Quantum Ultra Ceiling Concealed Ducted Split Heat Pump System Cooling capacity: 22,000 BTU/H with 19.0 SEER2 / 11.0 EER2 efficiency Heating capacity: 25,000 BTU/H with 10.0 HSPF2 / 3.34 COP2 efficiency Voltage: 208/230V, 60Hz, 1Ph Ceiling Concealed Mounted Ducted Air Conditioning & Heating System Variable-Speed DC Inverter Driven Performance Factory-Precharged with Environmentally Friendly R454b Refrigerant Ultra Low Ambient Range Operation (As low as -13°F in Heating / As high as 131°F in Cooling) Features Heat Pump with Cooling, Heating, Dry, and Ventilation Modes Dual-Drainage Ports Washable, Reusable Air Filters Dual-Axis Airflow (Motorized Up-Down and Left-Right Louvers) Functional Remote with: ECO and SLEEP Modes, for Energy-Conservation Timer On/Off Control TURBO, for Times of High-Demand Self-Clean Cycle MEMORY, to Recall Favorite Settings IFEEL, to Detect and Adjust to Local Temperature Technical Information & Performance AHRI Certificate Energy Guide Submittal Sheet System Kit Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 22,000 BTU/h Cooling Capacity Range: 7,550~24,600 BTU/h Cooling SEER2: 19.0 BTU/W.h Cooling EER2: 11.0 BTU/W.h Heating Rated Capacity: 25,000 BTU/h Heating Capacity Range: 8,700~28,500 BTU/h Heating HSPF2 (Region IV/V): 10.0 / 8.8 BTU/W.h Heating C.O.P.2 (47°F/5°F): 3.34 / 2.0 W/W Refrigerant Type: R454b Recommended Room Size: 750~1,000 sq ft Minimum Room Size: 62 sq ft Piping Diameter: 5/8" (Gas) / 1/4" (Liquid) AHRI Reference: 217048765 Indoor Unit Part Number: RT024GLSILCFHG Air Flow (Turbo/Hi/Med/Lo/Mute): 741 / 623 / 558 / 529 / 470 CFM Sound Level (Turbo/Hi/Med/Lo/Mute): 41 / 38 / 34 dB(A) Product Dimensions (WDH): 43"-1/4 x 17"-3/4 x 7"-7/8 Inches Carton Dimensions (WDH): 50"-3/4 x 22"-1/4 x 9"-7/8 Inches Net / Gross Weight: 50.7 / 58.4 lbs Outdoor Unit Part Number: YN024GLSI24RPG Breaker Needed: 25A (double-pole) Sound Level: 54 dB(A) Net Dimensions (WDH): 38"-1/2 x 16"-5/8 x 31"-5/8 Inches Carton Dimensions (WDH): 40"-1/4 x 18"-7/8 x 31"-7/8 Inches Net / Gross Weight: 104.7 / 119.0 lbs Dimension Chart .st0 { fill: #fff; stroke: #ccc; stroke-miterlimit: 10; stroke-width: 1px; } .st1 { font-family: ArialMT, Arial; font-size: 28px; letter-spacing: 1px; } 43¼ 17¾ 7⅞ 38½ 16⅝ 31⅝ 2¼ ¾ 8½


Pioneer® Quantum Ultra™ 18,000 BTU 20.5 SEER2 230V Floor/Ceiling/Low-Wall Ductless Mini-Split Air Conditioner Inverter Heat Pump Full Set - Add Standa

Summary High Efficiency Quantum Ultra Floor/Ceiling/Low-Wall Ductless Split Heat Pump System Cooling capacity: 18,000 BTU/H with 20.5 SEER2 / 11.7 EER2 efficiency Heating capacity: 18,000 BTU/H with 9.0 HSPF2 / 2.8 COP2 efficiency Voltage: 208/230V, 60Hz, 1Ph Floor/Ceiling/Low-Wall Mounted Ductless Air Conditioning & Heating System Variable-Speed DC Inverter Driven Performance Factory-Precharged with Environmentally Friendly R454b Refrigerant Ultra Low Ambient Range Operation (As low as -13°F in Heating / As high as 131°F in Cooling) Features Heat Pump with Cooling, Heating, Dry, and Ventilation Modes Dual-Drainage Ports Washable, Reusable Air Filters Dual-Axis Airflow (Motorized Up-Down and Left-Right Louvers) Functional Remote with: ECO and SLEEP Modes, for Energy-Conservation Timer On/Off Control TURBO, for Times of High-Demand Self-Clean Cycle MEMORY, to Recall Favorite Settings IFEEL, to Detect and Adjust to Local Temperature Technical Information & Performance AHRI Certificate Energy Guide Submittal Sheet System Kit Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 18,000 BTU/h Cooling Capacity Range: 4,550~20,200 BTU/h Cooling SEER2: 20.5 BTU/W.h Cooling EER2: 11.7 BTU/W.h Heating Rated Capacity: 18,000 BTU/h Heating Capacity Range: 2,910~22,840 BTU/h Heating HSPF2 (Region IV/V): 9.0 / 8.2 BTU/W.h Heating C.O.P.2 (47°F/5°F): 2.8 / 1.85 W/W Refrigerant Type: R454b Recommended Room Size: 500~750 sq ft Minimum Room Size (Ceiling Suspended): 51 sq ft Minimum Room Size (Floor/Low Wall): 195 sq ft Piping Diameter: 1/2" (Gas) / 1/4" (Liquid) AHRI Reference: 217048766 Indoor Unit Part Number: UT018GLSILCFHG Air Flow (Turbo/Hi/Med/Lo/Mute): 588 / 512 / 453 / 353 / 265 CFM Sound Level (Turbo/Hi/Med/Lo/Mute): 50 / 46 / 44 / 40 / 36 dB(A) Product Dimensions (WDH): 41"-1/2 x 26"-1/2 x 9"-1/4 Inches Carton Dimensions (WDH): 44"-1/2 x 26"-1/2 x 12" Inches Net / Gross Weight: 52.9 / 63.9 lbs Outdoor Unit Part Number: YN018GLSI24RPG Breaker Needed: 20A (double-pole) Sound Level: 53 dB(A) Net Dimensions (WDH): 36"-1/2 x 15" x 27"-1/2 Inches Carton Dimensions (WDH): 37"-3/8 x 16"-1/2 x 28"-7/8 Inches Net / Gross Weight: 90.4 / 97.0 lbs Dimension Chart .st0 { fill: #fff; stroke: #ccc; stroke-miterlimit: 10; stroke-width: 1px; } .st1 { font-family: ArialMT, Arial; font-size: 28px; letter-spacing: 1px; } 41½ 26½ 9¼ 36½ 15 27½ 2¼ ¾ 8½


Dual Split 24000 BTU 2-Ton Quantum Ultra Wi-Fi 24 SEER2 Energy-Star Multi (2) Zone Wall Mount Air Conditioner Heat Pump 230-Volt

Summary Pioneer brand multi split heat pump system, complete set. System components include: one multi zone outdoor unit, matching multiple wall mount indoor units, piping and accessory kits and remote controllers. Pioneer Quantum Ultra multi split systems are available in 5 versions; for 2, 3, 4, and 5 zones. Ultra-high efficiency inverter++ ductless multi split triple (3) zone heat pump system (paired with 2x indoor units to function effectively as a stronger 2-zone system) (x2) inside unit cooling capacity: 12,000 BTU/H nominal capacity, condensing system 27,000 BTU/H (Range: 4,500 minimum - 31,000 maximum) with 24 SEER2/12.0 EER2 efficiency Heating capacity: 28,000 BTU/H nominal (range 4,500 minimum - 33,000 maximum) with 10 HSPF/3.5 COP efficiency Voltage: 208 - 230-Volt, 60 hertz, 1 phase (standard household 2 line power, l1-l2-g) Energy-Star Certified and Wi-Fi Enabled Complete system set including: indoor (fan coil) section, outdoor (condenser) section, wireless remote controller with wi-fi, insulated flared line set with other installation accessories Unsurpassed support hotline covering installation, use, troubleshooting, warranty and parts issues Ultra low ambient system can heat with high capacity at -13°F ambient outdoor temperatures Pre-charged with eco-friendly R454-B refrigerant to support total combined attached lineset lengths up to 75 ft long Pioneer is the best choice for pros and homeowners with the highest ratings for consumer satisfaction Certified by: ETL, AHRI, DOE for safety, performance and efficiency Built with the latest technologies using pulse width modulation driven DC inverter compressor and variable speed DC inverter fan motors for high performance and low power consumption System Manuals Technical Brochure Service Manual Submittal Sheet Installation Manual (Multi-Split Addendum) AHRI Certificate Energy Guide


Triple Split 36000 BTU 3-Ton Quantum Ultra Wi-Fi 22.5 SEER2 Energy-Star Multi (3) Zone Wall Mount Air Conditioner Heat Pump 230-Volt

Summary Pioneer brand multi split heat pump system, complete set. System components include: one multi zone outdoor unit, matching multiple wall mount indoor units, piping and accessory kits and remote controllers. Pioneer Quantum Ultra multi split systems are available in 5 versions; for 2, 3, 4, and 5 zones. Ultra-high efficiency inverter++ ductless multi split quad (4) circuit heat pump system (paired with 3x indoor units to function effectively as a stronger 3-zone system) (x3) inside unit cooling capacity: 12,000 BTU/H nominal capacity, condensing system 35,000 BTU/H (Range: 5,500 minimum - 41,000 maximum) with 22.5 SEER2/12.0 EER2 efficiency Heating capacity: 36,000 BTU/H nominal (range 5,500 minimum - 41,000 maximum) with 9.5 HSPF2/3.5 COP2 efficiency Voltage: 208 - 230-Volt, 60 hertz, 1 phase (standard household 2 line power, l1-l2-g) Energy-Star Certified and Wi-Fi Enabled Complete system set including: indoor (fan coil) section, outdoor (condenser) section, wireless remote controller with wi-fi, insulated flared line set with other installation accessories Unsurpassed support hotline covering installation, use, troubleshooting, warranty and parts issues Ultra low ambient system can heat with high capacity at -13°F ambient outdoor temperatures Pre-charged with eco-friendly R454-B refrigerant to support total combined attached lineset lengths up to 100 ft long Pioneer is the best choice for pros and homeowners with the highest ratings for consumer satisfaction Certified by: ETL, AHRI, DOE for safety, performance and efficiency Built with the latest technologies using pulse width modulation driven DC inverter compressor and variable speed DC inverter fan motors for high performance and low power consumption System Manuals Technical Brochure Service Manual Submittal Sheet Installation Manual (Multi-Split Addendum) AHRI Certificate Energy Guide


Pioneer® Quantum Ultra™ 18,000 BTU 22 SEER2 230V Single-Way Ceiling Recessed Cassette Ductless Mini-Split Air Conditioner Inverter Heat Pump Full Set

Summary High Efficiency Quantum Ultra Single-Way Ceiling Recessed Cassette Split Heat Pump System Cooling capacity: 18,000 BTU/H with 22.2 SEER2 / 12.5 EER2 efficiency Heating capacity: 18,000 BTU/H with 12.2 HSPF2 / 3.3 COP2 efficiency Voltage: 208/230V, 60Hz, 1Ph Single-Way Ceiling Recessed Cassette Mounted Ductless Air Conditioning & Heating System Variable-Speed DC Inverter Driven Performance Factory-Precharged with Environmentally Friendly R454b Refrigerant Standard Ambient Range Operation (As low as -13°F in Heating / As high as 131°F in Cooling) Features Heat Pump with Cooling, Heating, Dry, and Ventilation Modes Dual-Drainage Ports Washable, Reusable Air Filters Dual-Axis Airflow (Motorized Up-Down and Left-Right Louvers) Functional Remote with: ECO and SLEEP Modes, for Energy-Conservation Timer On/Off Control TURBO, for Times of High-Demand Self-Clean Cycle MEMORY, to Recall Favorite Settings IFEEL, to Detect and Adjust to Local Temperature Technical Information & Performance AHRI Certificate Energy Guide Submittal Sheet System Kit Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 18,000 BTU/h Cooling Capacity Range: 4,000~18,800 BTU/h Cooling SEER2: 22.2 BTU/W.h Cooling EER2: 12.5 BTU/W.h Heating Rated Capacity: 18,000 BTU/h Heating Capacity Range: 7,600~22,800 BTU/h Heating HSPF2 (Region IV/V): 12.2 / 8.6 BTU/W.h Heating C.O.P.2 (47°F/5°F): 3.3 / 2.24 W/W Refrigerant Type: R454b Recommended Room Size: 500~750 sq ft Minimum Room Size: 54 sq ft Piping Diameter: 1/2" (Gas) / 1/4" (Liquid) AHRI Reference: 218010988 Indoor Unit Part Number: CK018GMSILDFHG Air Flow (Turbo/Hi/Med/Lo/Mute): 400 / 352 / 300 / 258 CFM Sound Level (Turbo/Hi/Med/Lo/Mute): 48 / 44 / 41 / 30 / 24 dB(A) Product Dimensions (WDH): 50"-3/8 x 13"-1/4 x 10" Inches Carton Dimensions (WDH): 57"-5/8 x 22"-1/2 x 22"-5/8 Inches Net / Gross Weight: 45.5 / 83.0 lbs Decorative Panel Part Number: --- Product Dimensions (WDH): 25"-5/8 x 25"-5/8 x 2"-3/8 Inches Carton Dimensions (WDH): Packed with the indoor unit inside same carton Net / Gross Weight: 15.0 / N/A lbs Outdoor Unit Part Number: YN018GMSI24RPG Breaker Needed: 20A (double-pole) Sound Level: 58 dB(A) Net Dimensions (WDH): 35" x 13"-1/2 x 26"-1/2 Inches Carton Dimensions (WDH): 39"-1/4 x 15"-5/8 x 29"-1/8 Inches Net / Gross Weight: 92.6 / 100.3 lbs Dimension Chart .st0 { fill: #fff; stroke: #ccc; stroke-miterlimit: 10; stroke-width: 1px; } .st1 { font-family: ArialMT, Arial; font-size: 28px; letter-spacing: 1px; } 50⅜ 13¼ 10 25⅝ 25⅝ 2⅜ 35 13½ 26½ 2¼ ¾ 8½


Pioneer® Quantum Ultra™ 36,000 BTU 20 SEER2 230V 4-Way Ceiling Cassette Ductless Mini-Split Air Conditioner Inverter Heat Pump - 16 Ft.

Summary High Efficiency Quantum Ultra Four-Way Ceiling Recessed Cassette Split Heat Pump System Cooling capacity: 36,000 BTU/H with 20.0 SEER2 / 9.6 EER2 efficiency Heating capacity: 38,000 BTU/H with 10.3 HSPF2 / 3.31 COP2 efficiency Voltage: 208/230V, 60Hz, 1Ph Four-Way Ceiling Recessed Cassette Mounted Ductless Air Conditioning & Heating System Variable-Speed DC Inverter Driven Performance Factory-Precharged with Environmentally Friendly R454b Refrigerant Standard Ambient Range Operation (As low as -13°F in Heating / As high as 131°F in Cooling) Features Heat Pump with Cooling, Heating, Dry, and Ventilation Modes Dual-Drainage Ports Washable, Reusable Air Filters Dual-Axis Airflow (Motorized Up-Down and Left-Right Louvers) Functional Remote with: ECO and SLEEP Modes, for Energy-Conservation Timer On/Off Control TURBO, for Times of High-Demand Self-Clean Cycle MEMORY, to Recall Favorite Settings FOLLOW ME, to Detect and Adjust to Local Temperature Technical Information & Performance AHRI Certificate Energy Guide Submittal Sheet System Kit Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 36,000 BTU/h Cooling Capacity Range: 6,400~39,800 BTU/h Cooling SEER2: 20.0 BTU/W.h Cooling EER2: 9.6 BTU/W.h Heating Rated Capacity: 38,000 BTU/h Heating Capacity Range: 14,400~42,200 BTU/h Heating HSPF2 (Region IV/V): 10.3 / 7.9 BTU/W.h Heating C.O.P.2 (47°F/5°F): 3.31 / 2.2 W/W Refrigerant Type: R454b Recommended Room Size: 1,000~1,400 sq ft Minimum Room Size: 103 sq ft Piping Diameter: 3/4" (Gas) / 3/8" (Liquid) AHRI Reference: 218010991 Indoor Unit Part Number: CB036GMSILDFHG Air Flow (Turbo/Hi/Med/Lo/Mute): 1,042 / 948 / 853 / 753 / 659 CFM Sound Level (Turbo/Hi/Med/Lo/Mute): 54 / 52 / 47 / 40 / 36 dB(A) Product Dimensions (WDH): 32"-5/8 x 32"-5/8 x 9"-5/8 Inches Carton Dimensions (WDH): 35"-7/8 x 35"-7/8 x 11"-3/8 Inches Net / Gross Weight: 59.3 / 71.5 lbs Decorative Panel Product Dimensions (WDH): 37"-3/8 x 37"-3/8 x 2"-1/8 Inches Carton Dimensions (WDH): 40"-3/4 x 40"-3/4 x 3"-1/2 Inches Net / Gross Weight: 13.2 / 19.8 lbs Outdoor Unit Part Number: YN036GMSI20RUG Breaker Needed: 35A (double-pole) Sound Level: 63 dB(A) Net Dimensions (WDH): 37"-1/4 x 16"-1/4 x 31"-7/8 Inches Carton Dimensions (WDH): 42"-7/8 x 19"-5/8 x 34"-7/8 Inches Net / Gross Weight: 152.4 / 162.5 lbs Dimension Chart .st0 { fill: #fff; stroke: #ccc; stroke-miterlimit: 10; stroke-width: 1px; } .st1 { font-family: ArialMT, Arial; font-size: 28px; letter-spacing: 1px; } 32⅝ 32⅝ 9⅝ 37⅜ 37⅜ 2⅛ 37¼ 16¼ 31⅞ 2¼ ¾ 8½


Pioneer® Quantum Ultra™ 48,000 BTU 19 SEER2 230V 4-Way Ceiling Cassette Ductless Mini-Split Air Conditioner Inverter Heat Pump - 16 Ft.

Summary High Efficiency Quantum Ultra Four-Way Ceiling Recessed Cassette Split Heat Pump System Cooling capacity: 48,000 BTU/H with 19.0 SEER2 / 9.5 EER2 efficiency Heating capacity: 50,000 BTU/H with 9.9 HSPF2 / 2.96 COP2 efficiency Voltage: 208/230V, 60Hz, 1Ph Four-Way Ceiling Recessed Cassette Mounted Ductless Air Conditioning & Heating System Variable-Speed DC Inverter Driven Performance Factory-Precharged with Environmentally Friendly R454b Refrigerant Standard Ambient Range Operation (As low as -13°F in Heating / As high as 131°F in Cooling) Features Heat Pump with Cooling, Heating, Dry, and Ventilation Modes Dual-Drainage Ports Washable, Reusable Air Filters Dual-Axis Airflow (Motorized Up-Down and Left-Right Louvers) Functional Remote with: ECO and SLEEP Modes, for Energy-Conservation Timer On/Off Control TURBO, for Times of High-Demand Self-Clean Cycle MEMORY, to Recall Favorite Settings FOLLOW ME, to Detect and Adjust to Local Temperature Technical Information & Performance AHRI Certificate Energy Guide Submittal Sheet System Kit Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 48,000 BTU/h Cooling Capacity Range: 10,600~50,400 BTU/h Cooling SEER2: 19.0 BTU/W.h Cooling EER2: 9.5 BTU/W.h Heating Rated Capacity: 50,000 BTU/h Heating Capacity Range: 19,900~61,700 BTU/h Heating HSPF2 (Region IV/V): 9.9 / 7.7 BTU/W.h Heating C.O.P.2 (47°F/5°F): 2.96 / 2.11 W/W Refrigerant Type: R454b Recommended Room Size: 1,400~1,800 sq ft Minimum Room Size: 143 sq ft Piping Diameter: 3/4" (Gas) / 3/8" (Liquid) AHRI Reference: 218010992 Indoor Unit Part Number: CB048GMSILDFHG Air Flow (Turbo/Hi/Med/Lo/Mute): 1,236 / 1,124 / 1,018 / 800 / 689 CFM Sound Level (Turbo/Hi/Med/Lo/Mute): 56 / 52 / 50 / 42 / 38 dB(A) Product Dimensions (WDH): 32"-5/8 x 32"-5/8 x 11"-3/8 Inches Carton Dimensions (WDH): 35"-7/8 x 35"-7/8 x 13" Inches Net / Gross Weight: 64.5 / 76.1 lbs Decorative Panel Product Dimensions (WDH): 37"-3/8 x 37"-3/8 x 2"-1/8 Inches Carton Dimensions (WDH): 40"-3/4 x 40"-3/4 x 3"-1/2 Inches Net / Gross Weight: 13.2 / 19.8 lbs Outdoor Unit Part Number: YN048GMSI20RUG Breaker Needed: 40A (double-pole) Sound Level: 64 dB(A) Net Dimensions (WDH): 37"-1/2 x 16"-3/8 x 52"-1/2 Inches Carton Dimensions (WDH): 43"-1/8 x 19"-1/2 x 57"-1/2 Inches Net / Gross Weight: 208.8 / 239.8 lbs Dimension Chart .st0 { fill: #fff; stroke: #ccc; stroke-miterlimit: 10; stroke-width: 1px; } .st1 { font-family: ArialMT, Arial; font-size: 28px; letter-spacing: 1px; } 32⅝ 32⅝ 11⅜ 37⅜ 37⅜ 2⅛ 37½ 16⅜ 52½ 2¼ ¾ 8½


Pioneer® Quantum Ultra™ 36,000 BTU 20 SEER2 230V Floor/Ceiling/Low-Wall Ductless Mini-Split Air Conditioner Inverter Heat Pump - 16 Ft.

Summary High Efficiency Quantum Ultra Floor/Ceiling/Low-Wall Ductless Split Heat Pump System Cooling capacity: 36,000 BTU/H with 20.0 SEER2 / 10.1 EER2 efficiency Heating capacity: 38,000 BTU/H with 10.0 HSPF2 / 3.34 COP2 efficiency Voltage: 208/230V, 60Hz, 1Ph Floor/Ceiling/Low-Wall Mounted Ductless Air Conditioning & Heating System Variable-Speed DC Inverter Driven Performance Factory-Precharged with Environmentally Friendly R454b Refrigerant Ultra Low Ambient Range Operation (As low as -13°F in Heating / As high as 131°F in Cooling) Features Heat Pump with Cooling, Heating, Dry, and Ventilation Modes Dual-Drainage Ports Washable, Reusable Air Filters Dual-Axis Airflow (Motorized Up-Down and Left-Right Louvers) Functional Remote with: ECO and SLEEP Modes, for Energy-Conservation Timer On/Off Control TURBO, for Times of High-Demand Self-Clean Cycle MEMORY, to Recall Favorite Settings FOLLOW ME, to Detect and Adjust to Local Temperature Technical Information & Performance AHRI Certificate Energy Guide Submittal Sheet System Kit Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 36,000 BTU/h Cooling Capacity Range: 7,300~39,500 BTU/h Cooling SEER2: 20.0 BTU/W.h Cooling EER2: 10.1 BTU/W.h Heating Rated Capacity: 38,000 BTU/h Heating Capacity Range: 14,100~40,400 BTU/h Heating HSPF2 (Region IV/V): 10.0 / 7.7 BTU/W.h Heating C.O.P.2 (47°F/5°F): 3.34 / 2.17 W/W Refrigerant Type: R454b Recommended Room Size: 1,000~1,400 sq ft Minimum Room Size (Ceiling Suspended): 104 sq ft Minimum Room Size (Floor/Low Wall): 500 sq ft Piping Diameter: 3/4" (Gas) / 3/8" (Liquid) AHRI Reference: 218010995 Indoor Unit Part Number: UB036GMSILDFHG Air Flow (Turbo/Hi/Med/Lo/Mute): 1,224 / 1,089 / 989 / 765 / 663 CFM Sound Level (Turbo/Hi/Med/Lo/Mute): 50 / 49 / 44 / 37 / 33 dB(A) Product Dimensions (WDH): 65" x 26"-5/8 x 9"-1/4 Inches Carton Dimensions (WDH): 68"-3/8 x 30" x 12"-1/4 Inches Net / Gross Weight: 89.0 / 105.0 lbs Outdoor Unit Part Number: YN036GMSI20RUG Breaker Needed: 40A (double-pole) Sound Level: 63 dB(A) Net Dimensions (WDH): 37"-1/4 x 16"-1/4 x 31"-7/8 Inches Carton Dimensions (WDH): 42"-7/8 x 19"-5/8 x 34"-7/8 Inches Net / Gross Weight: 152.4 / 162.5 lbs Dimension Chart .st0 { fill: #fff; stroke: #ccc; stroke-miterlimit: 10; stroke-width: 1px; } .st1 { font-family: ArialMT, Arial; font-size: 28px; letter-spacing: 1px; } 65 26⅝ 9¼ 37¼ 16¼ 31⅞ 2¼ ¾ 8½


Pioneer® EStar™ 24,000 BTU 21 SEER2 Ductless Mini-Split Inverter++ Energy-Star Air Conditioner Heat Pump System Full Set 230V - 16 Ft

Overview Summary Ultra High Efficiency Inverter++ ductless mini split heat pump system Cooling capacity: 24,000 BTU/H with 21 SEER2 / 12.5 EER2 efficiency Heating capacity: 26,000 BTU/H with 9.0 HSPF2 / 3.05 COP2 efficiency Voltage: 208~230 V, 60 Hertz, 1Ph High Wall Mounted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Customizable length copper line set with flare connections Energy-Star Certified AHRI Estimated Annual Operating Costs: Cooling: $151.00 Heating: $550.00 [[SERIES]] What's Included Indoor Unit Outdoor Unit Wireless Remote Control Various Installation Kit Options Available Flare Connection Leak Guard Sealer Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 year compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 24,000 BTU/h Cooling Capacity Range: 9,200~25,000 BTU/h Cooling SEER2: 21 BTU/W.h Cooling EER2: 12.5 BTU/W.h Heating Rated Capacity: 26,000 BTU/h Heating Capacity Range: 10,350~26,410 BTU/h Heating HSPF2 (Region IV/V): 9.0 / 6.8 BTU/W.h Heating C.O.P.2 (47°F/5°F): 3.05 / 1.92 W/W Refrigerant Type: R410a Suitable Area: 600~950 Sq.F Indoor Unit Data Part Number: WS024GMFI22HLE Air Flow (Hi/Med/Lo): 618 / 471 / 324 CFM Sound Level (Hi/Med/Lo): 47.5 / 42.0 / 32.0 dB(A) Net Dimensions (WDH): 42.5 x 8.8 x 13.2 Inches Carton Dimensions (WDH): 45.5 x 12.3 x 16.3 Inches Net / Gross Weight: 30.2 / 37.9 Lbs Outdoor Unit Data Part Number: YN024GMFI22RPE Breaker Needed: 25A (double-pole) Sound Level: 61.0 dB(A) Net Dimensions (WDH): 37.2 x 16.2 x 31.8 Inches Carton Dimensions (WDH): 42.8 x 19.6 x 34.8 Inches Net / Gross Weight: 124.8 / 134.9 Lbs Manuals & Downloads Series Technical Brochure Series User Manual Series Installation Manual Series Service Manual Disassembly Guide AHRI Certificate Energy Guide


Pioneer® 9,000 BTU 21.5 SEER2 Ductless Mini-Split Inverter+ Energy-Star Air Conditioner Heat Pump System Full Set 115V - 16 Ft

Overview Summary High Efficiency Quantum Series Inverter+ ductless mini split heat pump system Cooling capacity: 9,000 BTU/H with 21.5 SEER2 / 12.5 EER2 efficiency Heating capacity: 10,000 BTU/H with 9.0 HSPF2 / 2.93 COP2 efficiency Voltage: 110~120V, 60Hz, 1Ph High Wall Mounted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Customizable length copper line set with flare connections Energy-Star Certified AHRI Estimated Annual Operating Costs: Cooling: $58.00 Heating: $211.00 [[SERIES]] What's included with the Pioneer 9,000 BTU 20.5 SEER 115V ductless mini-split inverter and air conditioner heat pump system full set: Indoor Unit Outdoor Unit Wireless Remote Control Various Installation Kit Options Available Flare Connection Leak Guard Sealer Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 year compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 110~120V, 60Hz, 1Ph Cooling Rated Capacity: 9,000 BTU/h Cooling Capacity Range: 2,650~10,300 BTU/h Cooling SEER2: 21.5 BTU/W.h Cooling EER2: 12.5 BTU/W.h Heating Rated Capacity: 10,000 BTU/h Heating Capacity Range: 2,700~10,300 BTU/h Heating HSPF2 (Region IV/V): 9.0 / 6.9 BTU/W.h Heating C.O.P.2 (47°F/5°F): 2.93 / 1.89 W/W Refrigerant Type: R410A Suitable Area: 100~350 Sq.F Indoor Unit Data Part Number: WS009AMFI20HLD Air Flow (Hi/Med/Lo): 247 / 182 / 129 CFM Sound Level (Hi/Med/Lo): 38 / 32 / 25 dB(A) Net Dimensions (WDH): 28.43 x 7.36 x 11.42 Inches Carton Dimensions (WDH): 31.1 x 10.63 x 14.76 Inches Net / Gross Weight: 17.0 / 22.3 lbs Outdoor Unit Data Part Number: YN009AMFI20RPD Sound Level: 54.0 dB(A) Breaker Needed: 20A Single-Pole Net Dimensions (WDH): 30.2 x 11.8 x 21.8 Inches Carton Dimensions (WDH): 34.8 x 13.2 x 24 Inches Net / Gross Weight: 57.8 / 63.5 lbs Manuals & Downloads Technical Brochure User Manual Installation Manual Service Manual Disassembly Guide AHRI Certificate Energy Guide


Pioneer® 12,000 BTU 20.8 SEER2 Ductless Mini-Split Inverter+ Air Conditioner Heat Pump System Full Set 115V - 16 Ft

Overview Summary High Efficiency Quantum Series Inverter+ ductless mini split heat pump system Cooling capacity: 12,000 BTU/H with 20.8 SEER2 / 10.3 EER2 efficiency Heating capacity: 12,000 BTU/H with 8.7 HSPF2 / 3.13 COP2 efficiency Voltage: 110~120V, 60Hz, 1Ph High Wall Mounted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Customizable length copper line set with flare connections AHRI Estimated Annual Operating Costs: Cooling: $79.00 Heating: $242.00 [[SERIES]] What's Included Indoor Unit Outdoor Unit Wireless Remote Control Various Installation Kit Options Available Flare Connection Leak Guard Sealer Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 year compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 110~120V, 60Hz, 1Ph Cooling Rated Capacity: 12,000 BTU/h Cooling Capacity Range: 4,300~12,600 BTU/h Cooling SEER2: 20.8 BTU/W.h Cooling EER2: 10.3 BTU/W.h Heating Rated Capacity: 12,000 BTU/h Heating Capacity Range: 4,000~12,500 BTU/h Heating HSPF2 (Region IV/V): 8.7 / 6.6 BTU/W.h Heating C.O.P.2 (47°F/5°F): 3.13 / 1.91 W/W Refrigerant Type: R410A/30 Suitable Area: 300~450 Sq.F Indoor Unit Data Part Number: WS012AMFI20HLD Air Flow (Turbo/Hi/Med/Lo): 341 / 309 / 206 / 176 CFM Sound Level (Hi/Med/Lo): 41.5 / 30.5 / 26.0 dB(A) Net Dimensions (WDH): 31.57 x 7.44 x 11.69 Inches Carton Dimensions (WDH): 34.45 x 11.22 x 14.96 Inches Net / Gross Weight: 20 / 25 lbs Outdoor Unit Data Model Number: YN012AMFI20RPD Sound Level: 55.5 dB(A) Net Dimensions (WDH): 30.1 x 11.93 x 21.85 Inches Carton Dimensions (WDH): 34.8 x 13.25 x 24 Inches Net / Gross Weight: 62.2 / 67.7 lbs Breaker Needed: 20A (single-pole) Manuals & Downloads Technical Brochure User Manual Installation Manual Service Manual Disassembly Guide AHRI Certificate Energy Guide


Pioneer® 12,000 BTU 21.4 SEER2 Ductless Mini-Split Inverter+ Air Conditioner Heat Pump System Full Set 230V - 16 Ft

Overview Summary High Efficiency Quantum Series Inverter+ ductless mini split heat pump system Cooling capacity: 12,000 BTU/H with 21.4 SEER2 / 10.8 EER2 efficiency Heating capacity: 12,000 BTU/H with 9.1 HSPF2 / 3.23 COP2 efficiency Voltage: 208~230V, 60Hz, 1Ph High Wall Mounted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Customizable length copper line set with flare connections AHRI Estimated Annual Operating Costs: Cooling: $77.00 Heating: $254.00 [[SERIES]] What's Included Indoor Unit Outdoor Unit Wireless Remote Control Various Installation Kit Options Available Flare Connection Leak Guard Sealer Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 year compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 12,000 BTU/h Cooling Capacity Range: 3,800~12,850 BTU/h Cooling SEER2: 21.40 BTU/W.h Cooling EER2: 10.80 BTU/W.h Heating Rated Capacity: 12,000 BTU/h Heating Capacity Range: 2,730~12,500 BTU/h Heating HSPF2 (Region IV/V): 9.1 / 6.9 BTU/W.h Heating C.O.P.2 (47°F/5°F): 3.23 / 1.68 W/W Refrigerant Type: R410A/28.6 oz. Suitable Area: 250~450 Sq.F Indoor Unit Data Part Number: WS012GMFI20HLD Air Flow (Hi/Med/Lo): 317 / 207 / 144 CFM Sound Level (Hi/Med/Lo): 37 / 30 / 22.5 dB(A) Net Dimensions (WDH): 31"-1/2 x 7"-3/8 x 11"-5/8 Inches Carton Dimensions (WDH): 34"-1/2 x 11"-1/4 x 15" Inches Net / Gross Weight: 19.8 / 25 Lbs Outdoor Unit Data Part Number: YN012GMFI20RPD Sound Level: 55.5 dB(A) Net Dimensions (WDH): 30"-1/8 x 11"-7/8 x 21"-7/8 Inches Carton Dimensions (WDH): 34"-7/8 x 13"-1/4 x 24" Inches Net / Gross Weight: 59.3 / 64.8 lbs Breaker Needed: 15A (double-pole) Manuals & Downloads Technical Brochure User Manual Installation Manual Service Manual Disassembly Guide AHRI Certificate Energy Guide


Pioneer® 18,000 BTU 19 SEER2 Ductless Mini-Split Inverter+ Air Conditioner Heat Pump System Full Set 230V - 16 Ft

Overview Summary High Efficiency Quantum Series Inverter+ ductless mini split heat pump system inverter and air conditioner heat pump system full set Cooling capacity: 18,000 BTU/H with 19 SEER2 / 10.5 EER2 efficiency Heating capacity: 18,800 BTU/H with 8.7 HSPF2 / 2.93 COP2 efficiency Voltage: 208~230V, 60Hz, 1Ph High Wall Mounted Air Conditioning & Heating System Variable Speed DC high-efficiency Inverter Operation Mode Customizable length copper line set with flare connections AHRI Estimated Annual Operating Costs: Cooling: $125.00 Heating: $397.00 [[SERIES]] What's Included Indoor Unit Outdoor Unit Wireless Remote Control Various Installation Kit Options Available Flare Connection Leak Guard Sealer Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 year compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 18,000 BTU/h Cooling Capacity Range: 3,900~20,000 BTU/h Cooling SEER2: 19 BTU/W.h Cooling EER2: 10.5 BTU /W.h Heating Rated Capacity: 18,800 BTU/h Heating Capacity Range: 6,300~19,400 BTU/h Heating HSPF2 (Region IV/V): 8.7 / 6.8 BTU/W.h Heating C.O.P.2 (47°F/5°F): 2.93 / 2.1 W/W Refrigerant Type: R410A/47.6 oz. Suitable Area: 400~650 Sq.F Indoor Unit Data Model Number: WS018GMFI20HLD Air Flow (Hi/Med/Lo): 388 / 259 / 218 CFM Sound Level (Hi/Med/Lo): 43.5 / 34.5 / 30.0 dB(A) Net Dimensions (WDH): 38" x 8"-1/2 x 12"-1/2 Carton Dimensions (WDH): 41"-1/8 x 12" x 16"-1/8 Net / Gross Weight: 23.8 / 31.5 lbs Outdoor Unit Data Model Number: YN018GMFI20RPD Sound Level: 57 dB(A) Net Dimensions (WDH): 31"-5/8 x 13" x 21"-7/8 Carton Dimensions (WDH): 36" x 14"-5/8 x 24"-1/4 Net / Gross Weight: 73.9 / 79.8 lbs Breaker Needed: 20A (double-pole) Manuals & Downloads Technical Brochure User Manual Installation Manual Service Manual Disassembly Guide AHRI Certificate Energy Guide


Pioneer® 36,000 BTU 17.5 SEER2 Ductless Mini-Split Inverter+ Air Conditioner Heat Pump System Full Set 230V - 16 Ft

Overview Summary High Efficiency Quantum Series Inverter+ ductless mini split heat pump system Cooling capacity: 36,000 BTU/H with 17.5 SEER2 / 8.5 EER2 efficiency Heating capacity: 36,000 BTU/H with 8.7 HSPF2 / 2.47 COP2 efficiency Voltage: 208~230V, 60Hz, 1Ph High Wall Mounted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Customizable length copper line set with flare connections AHRI Estimated Annual Operating Costs: Cooling: $272.00 Heating: $645.00 [[SERIES]] What's Included Ductless Wall-Type Indoor Air Handler Unit Outdoor Heat Pump Condensing Unit Wireless Handheld Remote Control Various Installation Kit Options Available Flare Connection Leak Guard Sealer Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 year compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 36,000 BTU/h (3-Ton) Cooling Capacity Range: 8,900~36,300 BTU/h Cooling SEER2: 17.5 BTU/W.h Cooling EER2: 8.5 BTU/W.h Heating Rated Capacity: 36,000 BTU/h (3-Ton) Heating Capacity Range: 11,400~37,800 BTU/h Heating HSPF2 (Region IV/V): 8.7 / 6.8 BTU/W.h Heating C.O.P.2 (47°F/5°F): 2.47 / 1.97 W/W Refrigerant Type: R410A/120 Suitable Area: 900~1,250 Sq.F Indoor Unit Data Model Number: WS036GMFI20HLD Air Flow (Turbo/Hi/Med/Lo): 882 / 732 / 518 / 400 CFM Sound Level (Hi/Med/Lo): 56.5 / 54.5 / 40 dB(A) Net Dimensions (WDH): 49"-1/2 x 11"-1/8 x 14"-1/4 Inches Carton Dimensions (WDH): 52"-3/4 x 17"-3/4 x 15"-1/4 Inches Net / Gross Weight: 40 / 52.5 lbs Outdoor Unit Data Model Number: YN036GMFI20RPD Sound Level: 63.5 dB(A) Breaker Needed: 30A (double-pole) Net Dimensions (WDH): 37"-1/4 x 16"-1/4 x 31"-7/8 Inches Carton Dimensions (WDH): 42"-7/8 x 19"-5/8 x 34" Inches Net / Gross Weight: 150 / 159 lbs Manuals & Downloads Technical Brochure User Manual Installation Manual Service Manual Disassembly Guide AHRI Certificate Energy Guide


Pioneer® Triple (3) Zone Quantum Series Outdoor Section 23.5 SEER2 Multi Split Inverter++ Energy-Star Air Conditioner & Heat Pump 230V

Overview Summary OUTDOOR SECTION ONLY for Triple (3) Zone Quantum/Free-Match Series Ultra High Efficiency DC Inverter++ version Cooling capacity: 27,000 BTU/H Nominal (Range: 8,500 MIN ~ 32,000 MAX) with 23.5 SEER2 / 12.2 EER2 efficiency Heating capacity: 28,000 BTU/H Nominal (Range: 8,200 MIN ~ 35,000 MAX) with 9.2 HSPF2 efficiency Voltage: 208~230 V, 60 Hertz, 1 Ph Factory charged for up to 25’ line set per circuit Whisper Quiet Operation [[REFRIGERANT]] Technical Information Certifications Performance Data Power Supply: 208~230V, 60Hz, 1Ph Communication Protocol: Current Loop Min-Max Load Attached: 18,000~36,000 BTU/h Cooling Rated Capacity: 27,000 BTU/h Cooling Capacity Range: 8,500~32,000 BTU/h Cooling SEER2 (Ductless): 23.5 BTU/W.h Cooling EER2 (Ductless): 12.2 BTU/W.h Heating Rated Capacity: 28,000 BTU/h Heating Capacity Range: 3,690~32,860 BTU/h Heating HSPF2 (Ductless): 9.2 BTU/W.h Refrigerant Type: R410a Suitable Area: 800~1,200 Sq.F Sound Level: 60.0 dB(A) Net Dimensions (WDH): 37.2 x 16.2 x 31.8 Inches Carton Dimensions (WDH): 42.8 x 19.6 x 34.8 Inches Net / Gross Weight: 140 / 151 Lbs Matching Indoor Models Triple Zone Combinations Rating Two Units Three units Wall: 9 + 9 + 9 9 + 9 9 + 9 + 9 Ducted: 9 + 9 + 9 9 + 12 9 + 9 + 12 9 + 18 9 + 9 + 18 12 + 12 9 + 12 + 12 12 + 18 12 + 12 + 12 18 + 18 9,000 BTU Compatible Units Wall Mounted: WS009GMFI22HLE (31.5 x 7.4 x 11.6 inches) Ceiling Cassette: CB009GMFILCFHD (22.5 x 22.5 x 10.3 inches) Concealed Ducted: RB009GMFILDFHD (27.5 x 25.0 x 8.3 inches) One-Way Cassette: CK009GMFILCFHD (13.25 x 50.25 x 9 Inches) 12,000 BTU Compatible Units Wall Mounted: WS012GMFI22HLE (31.5 x 7.4 x 11.6 inches) Ceiling Cassette: CB012GMFILCFHD (22.5 x 22.5 x 10.3 inches) Floor-Console: FB012GMFILDFHE (27.5 x 23.6 x 8.3 inches) Concealed Ducted: RB012GMFILDFHD (27.5 x 25.0 x 8.3 inches) One-Way Cassette: CK012GMFILCFHD (13.25 x 50.25 x 9 Inches) 18,000 BTU Compatible Units Wall Mounted: WS018GMFI22HLE (42.5 x 8.8 x 13.2 inches) Ceiling Cassette: CB018GMFILCFHD (22.5 x 22.5 x 10.3 inches) Concealed Ducted: RB018GMFILDFHD (36.3 x 25.0 x 8.3 inches) Floor-Console: FB018GMFILDFHE (31.25 x 24.5 x 7.8 inches) Flex-Mount: UB018GMFILCFHD (42.0 x 26.5 x 9.3 inches) One-Way Cassette: CK018GMFILCFHD (13.25 x 50.25 x 9 Inches) Min. / Max. Loading 18,000 / 36,000 BTU/h. Notes Every indoor unit attached will operate at a random, self regulated capacity, based on the actual demand it measures from the zone it is serving (Between 30% to 100% of its rated capacity or OFF). Outdoor unit will also self regulate its output capacity, based on the total demand it reads from all of the simultaneously running indoor units at any given moment. With multi split systems, the total demand from the outdoor unit, shall seldomly exceed 67% of the total available capacity of the combined indoor unit group due to load fluctuations. Although very seldom, if and when the total demand from the combined indoor group exceeds the rated capacity of the outdoor unit, the capacity of the each indoor unit will be annotated accordingly. For high demand heating applications, max loading limits may need to be reduced by 10-15 % to avoid under-performance risks at some extreme conditions. Manuals & Downloads Technical Brochure User Manual Installation Manual Service Manual Wiring Diagram AHRI Certificate Ductless Ducted Mixed Energy Guide Ductless Ducted Mixed


Pioneer® Quint (5) Zone Quantum Series Outdoor Section 21.1 SEER2 Multi Split Inverter++ Air Conditioner & Heat Pump 230V

Overview Summary OUTDOOR SECTION ONLY for Quint (5) Zone Quantum/Free-Match Series Ultra High Efficiency DC Inverter++ version Cooling capacity: 48,000 BTU/H Nominal (Range: 11,600 MIN ~ 49,700 MAX) with 21.1 SEER2 / 11 EER2 efficiency Heating capacity: 48,000 BTU/H Nominal (Range: 33,000 MIN ~ 53,900 MAX) with 9.5 HSPF2 efficiency Voltage: 208~230 V, 60 Hertz, 1 Ph Factory charged for up to 25’ line set per circuit Whisper Quiet Operation [[REFRIGERANT]] Technical Information Certifications Performance Data Power Supply: 208~230V, 60Hz, 1Ph Communication Protocol: Current Loop Min-Max Load Attached: 36,000~64,000 BTU/h Cooling Rated Capacity: 48,000 BTU/h Cooling Capacity Range: 11,600~49,700 BTU/h Cooling SEER2 (Ductless): 21.1 BTU/W.h Cooling EER2 (Ductless): 11.0 BTU/W.h Heating Rated Capacity: 48,000 BTU/h Heating Capacity Range: 33,000~52,900 BTU/h Heating HSPF2 (Ductless): 9.5 BTU/W.h Refrigerant Type: R410a Suitable Area: 1,600~2,000 Sq.F Sound Level: 62.0 dB(A) Net Dimensions (WDH): 37.2 x 16.4 x 52.3 Inches Carton Dimensions (WDH): 43.2 x 19.5 x 58.3 Inches Net / Gross Weight: 225 / 257 Lbs Matching Indoor Models Quint Zone Combinations Rating Two Units Three units Four units Five units Wall: 9 + 9 + 9 + 9 + 9 18 + 18 9 + 9 + 18 9 + 9 + 9 + 9 9 + 9 + 9 + 9 + 9 Ducted: 9 + 9 + 9 + 9 + 9 18 + 24 9 + 9 + 24 9 + 9 + 9 + 12 9 + 9 + 9 + 9 + 12 24 + 24 9 + 12 + 12 9 + 9 + 9 + 18 9 + 9 + 9 + 9 + 18 9 + 12 + 18 9 + 9 + 9 + 24 9 + 9 + 9 + 9 + 24 9 + 12 + 24 9 + 9 + 12 + 12 9 + 9 + 9 + 12 + 12 9 + 18 + 18 9 + 9 + 12 + 18 9 + 9 + 9 + 12 + 18 9 + 18 + 24 9 + 9 + 12 + 24 9 + 9 + 9 + 18 + 18 9 + 24 + 24 9 + 9 + 18 + 18 9 + 9 + 12 + 12 + 12 12 + 12 + 12 9 + 9 + 18 + 24 9 + 9 + 12 + 12 + 18 12 + 12 + 18 9 + 12 + 12 + 12 9 + 12 + 12 + 12 + 12 12 + 12 + 24 9 + 12 + 12 + 18 9 + 12 + 12 + 12 + 18 12 + 18 + 18 9 + 12 + 12 + 24 12 + 12 + 12 + 12 + 12 12 + 18 + 24 9 + 12 + 18 + 18 12 + 24 + 24 9 + 18 + 18 + 18 18 + 18 + 18 12 + 12 + 12 + 12 18 + 18 + 24 12 + 12 + 12 + 18 12 + 12 + 12 + 24 12 + 12 + 18 + 18 9,000 BTU Compatible Units Wall Mounted: WS009GMFI22HLE (31.5 x 7.4 x 11.6 inches) Ceiling Cassette: CB009GMFILCFHD (22.5 x 22.5 x 10.3 inches) Concealed Ducted: RB009GMFILDFHD (27.5 x 25.0 x 8.3 inches) One-Way Cassette: CK009GMFILCFHD (13.25 x 50.25 x 9 Inches) 12,000 BTU Compatible Units Wall Mounted: WS012GMFI22HLE (31.5 x 7.4 x 11.6 inches) Ceiling Cassette: CB012GMFILCFHD (22.5 x 22.5 x 10.3 inches) Floor-Console: FB012GMFILDFHE (27.5 x 23.6 x 8.3 inches) Concealed Ducted: RB012GMFILDFHD (27.5 x 25.0 x 8.3 inches) One-Way Cassette: CK012GMFILCFHD (13.25 x 50.25 x 9 Inches) 18,000 BTU Compatible Units Wall Mounted: WS018GMFI22HLE (42.5 x 8.8 x 13.2 Inches) Ceiling Cassette: CB018GMFILCFHD (22.5 x 22.5 x 10.3 inches) Concealed Ducted: RB018GMFILDFHD (36.3 x 25.0 x 8.3 inches) Floor-Console: FB018GMFILDFHE (31.25 x 24.5 x 7.8 inches) Flex-Mount: UB018GMFILCFHD (42.0 x 26.5 x 9.3 inches) One-Way Cassette: CK018GMFILCFHD (13.25 x 50.25 x 9 Inches) 24,000 BTU Compatible Units Wall Mounted: WS024GMFI22HLE (42.5 x 8.8 x 13.2 Inches) Ceiling Cassette: CB024GMFILDFHE (33.0 x 33.0 x 8.0 inches) Concealed Ducted: RB024GMFILDFHD (36.3 x 25.0 x 10.6 inches) Flex-Mount: UB024GMFILCFHD (42.0 x 26.5 x 9.3 inches) Min. / Max. Loading 32,000 / 48,000 BTU/h. Limitations Do not exceed two pieces of 24,000 BTU/h Indoor Unit Notes Every indoor unit attached will operate at a random, self regulated capacity, based on the actual demand it measures from the zone it is serving (Between 30% to 100% of its rated capacity or OFF). Outdoor unit will also self regulate its output capacity, based on the total demand it reads from all of the simultaneously running indoor units at any given moment. With multi split systems, the total demand from the outdoor unit, shall seldomly exceed 67% of the total available capacity of the combined indoor unit group due to load fluctuations. Although very seldom, if and when the total demand from the combined indoor group exceeds the rated capacity of the outdoor unit, the capacity of the each indoor unit will be annotated accordingly. For high demand heating applications, max loading limits may need to be reduced by 10-15 % to avoid under-performance risks at some extreme conditions. Manuals & Downloads Technical Brochure User Manual Installation Manual Service Manual AHRI Certificate Ductless Ducted Mixed Energy Guide Ductless Ducted Mixed


Floor Mounting Base Kit for Split Air Conditioning Systems - 9,000 - 12,000 BTU

Overview Summary Mount directly onto concrete or leave unfastened as desired Outer rubber shell provides superior vibration absorption Dual heavy-duty weighted block-style mounting set Elevates system while maintaining a low profile Built-in leveler to ensure perfectly horizontal mounting Weight RBASE2X5-18-2P 11 lbs RBASE2X5-20-3P 13 lbs RBASE3X6-18-4P 19 lbs


Floor Mounting Base Kit for Split Air Conditioning Systems - 18,000 - 24,000 BTU


Pioneer® 24,000 BTU Ducted Central Split Inverter+ Air Handler Unit Inside Section 230V

Overview Summary Air Handler Unit indoor section of DYR1824GMFI18R set series. This is not a full system, only the partial section of a complete set! Highlights Compatible with any standard 24V wall thermostat Universal match for all AC heat pumps of matching capacity Dual electric racks accept 5, 7.5, and 10kW electric heaters Multi-position, field convertible (vertical, horizontal, downflow) Outdoor Unit Data Model: DR024GHFD18HT2 Sound Level: 55 dB(A) Throttle Type: TXV Net Dimensions (WDH): 19-5/8 x 21-5/8 x 46-1/8 Inches Carton Dimensions (WDH): 22-1/2 x 21-5/8 x 49-5/8 Inches Net / Gross Weight: 135.5 / 158.6 Lbs Manuals & Downloads Series Technical Brochure Indoor Section Installation Manual Indoor Section Service Manual


Pioneer® 36,000 BTU Ducted Central Split Inverter+ Air Handler Unit Inside Section 230V

Overview Summary Air Handler Unit indoor section of DYR3036GMFI18R set series. This is not a full system, only the partial section of a complete set! Highlights Compatible with any standard 24V wall thermostat Universal match for all AC heat pumps of matching capacity Dual electric racks accept 5, 7.5, and 10kW electric heaters Multi-position, field convertible (vertical, horizontal, downflow) Outdoor Unit Data Model: DR036GHFD18HT2 Sound Level: 57 dB(A) Throttle Type: TXV Net Dimensions (WDH): 19-5/8 x 21-5/8 x 46-1/8 Inches Carton Dimensions (WDH): 22-1/2 x 21-5/8 x 49-5/8 Inches Net / Gross Weight: 140 / 163.1 Lbs Manuals & Downloads Series Technical Brochure Indoor Section Installation Manual Indoor Section Service Manual


Pioneer® 24,000 BTU 17 SEER2 Ducted Central Split Inverter+ Condenser AC Heat Pump Outside Section 230V

Overview Summary Outdoor unit section of DYR1824GMFI18R set series. This is not a full system, only the partial section of a complete set! Outdoor Unit Data Model: YH1824GHFD18R2 Sound Level: 57 dB(A) Metering Device: EXV Net Dimensions (WDH): 33-7/8 x 12-1/4 x 26-3/8 Inches Carton Dimensions (WDH): 39 x 17-3/4 x 28-3/4 Inches Net / Gross Weight: 135 / 159 Lbs Manuals & Downloads Series Technical Brochure Outdoor Section Installation Manual Outdoor Section Service Manual


Pioneer® 36,000 BTU 18 SEER2 Ducted Central Split Inverter+ Condenser AC Heat Pump Outside Section 230V

Overview Summary Outdoor unit section of DYR3036GMFI18R set series. This is not a full system, only the partial section of a complete set! Outdoor Unit Data Model: YH3036GHFD18R2 Sound Level: 57 dB(A) Metering Device: EXV Net Dimensions (WDH): 37-3/8 x 13-3/8 x 33 Inches Carton Dimensions (WDH): 43-3/4 x 18-1/8 x 36-1/4 Inches Net / Gross Weight: 148 / 159 Lbs Manuals & Downloads Series Technical Brochure Outdoor Section Installation Manual Outdoor Section Service Manual


Pioneer® 56,000 BTU 17 SEER2 Ducted Central Split Inverter+ Condenser AC Heat Pump Outside Section 230V

Overview Summary Outdoor unit section of DYR4860GMFI18R set series. This is not a full system, only the partial section of a complete set! Outdoor Unit Data Model: YH4860GHFD18R2 Sound Level: 60 dB(A) Metering Device: EXV Net Dimensions (WDH): 37-3/8 x 13-3/8 x 54-5/8 Inches Carton Dimensions (WDH): 43-3/4 x 18-1/8 x 60-1/4 Inches Net / Gross Weight: 251 / 278 Lbs Manuals & Downloads Series Technical Brochure Outdoor Section Installation Manual Outdoor Section Service Manual


Pioneer® Diamante Pro Series 9,000 BTU 19 SEER2 Ductless Mini-Split Air Conditioner Inverter+ Heat Pump Full Set 115V with 16 Ft. Kit

Overview Summary High Efficiency Diamante Pro Ductless Mini Split Heat Pump System Cooling capacity: 9,000 BTU/H with 19 SEER2 / 10 EER2 efficiency Heating capacity: 10,000 BTU/H with 8.5 HSPF / 3.41 COP efficiency Voltage: 110/120V, 60Hz, 1Ph High Wall Mounted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Low Ambient Unit (-13°F) AHRI Estimated Annual Operating Costs: Cooling: $59.00 Heating: $191.00 [[SERIES]] What's Included Indoor Unit Outdoor Unit Wireless Remote Control (with wall holder and batteries) 16 Ft. Copper Lines 16 Ft. Electrical Wire 10 Ft. Drain for indoor/outdoor Wall Passage Sleeve Putty for Wall Hole Leak Guard Sealer Wrapping Tape Installation Manual User’s Manual Our Guarantee 5 years Warranty for Parts 5 years Warranty for Compressor Features [[FEATURES]] Technical Information Performance Data Power Supply: 115V, 60Hz, 1Ph Cooling Rated Capacity: 9,000 BTU/h Cooling Capacity Range: 5,800~10,300 BTU/h Cooling SEER2: 19.0 BTU/W.h Cooling EER2: 10.0 BTU/W.h Heating Rated Capacity: 10,000 BTU/h Heating Capacity Range: 5,400~10,900 BTU/h Heating HSPF2 (Region IV/V): 8.5 / 7.0 BTU/W.h Heating C.O.P.2 (47°F/5°F): 3.41 / 1.75 W/W Refrigerant Type: R410A/28.6 Oz. Suitable Area: 100~350 Sq.F Indoor Unit Data Part Number: WT009ALFI19HLE Air Flow (Hi/Med/Lo): 353 / 288 / 250 CFM Sound Level (Hi/Med/Lo): 38 / 35 / 32 dB(A) Net Dimensions (WDH): 32 x 8-1/8 x 11-1/2 Inches Carton Dimensions (WDH): 34-7/8 x 11 x 14-1/2 Inches Net / Gross Weight: 19.8 / 24.2 lbs Outdoor Unit Data Part Number: YN009ALFI19RPE Breaker Needed: 20A (single-pole) Sound Level: 50 dB(A) Net Dimensions (WDH): 28-5/8 x 12 x 21-5/8 Inches Carton Dimensions (WDH): 33-1/2 x 14-1/8 x 24 Inches Net / Gross Weight: 60.6 / 69.5 lbs Manuals & Documents Technical Brochure User & Installation Manual Service Manual AHRI Certificate Energy Guide


Pioneer® Diamante Pro Series 12,000 BTU 19 SEER2 Ductless Mini-Split Air Conditioner Inverter+ Heat Pump Full Set 115V with 16 Ft. Kit

Overview Summary High Efficiency Diamante Pro Ductless Mini Split Heat Pump System Cooling capacity: 12,000 BTU/H with 19 SEER2 / 10 EER2 efficiency Heating capacity: 12,200 BTU/H with 8.5 HSPF2 / 3.21 COP2 efficiency Voltage: 110/120V, 60Hz, 1Ph High Wall Mounted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Low Ambient Unit (-13°F) AHRI Estimated Annual Operating Costs: Cooling: $79.00 Heating: $254.00 [[SERIES]] What's Included Indoor Unit Outdoor Unit Wireless Remote Control (with wall holder and batteries) 16 Ft. Copper Lines 16 Ft. Electrical Wire 10 Ft. Drain for indoor/outdoor Wall Passage Sleeve Putty for Wall Hole Leak Guard Sealer Wrapping Tape Installation Manual User’s Manual Our Guarantee 5 years Warranty for Parts 5 years Warranty for Compressor Features [[FEATURES]] Technical Information Performance Data Power Supply: 110~120V, 60Hz, 1Ph Cooling Rated Capacity: 12,000 BTU/h Cooling Capacity Range: 3,600~13,200 BTU/h Cooling SEER2: 19.0 BTU/W.h Cooling EER2: 10.0 BTU/W.h Heating Rated Capacity: 12,200 BTU/h Heating Capacity Range: 3,700~13,500 BTU/h Heating HSPF2 (Region IV/V): 8.5 / 7.2 BTU/W.h Heating C.O.P.2 (47°F/5°F): 3.21 / 1.75 W/W Refrigerant Type: R410A Suitable Area: 200~450 Sq.F Indoor Unit Data Part Number: WT012ALFI19HLE Air Flow (Hi/Med/Lo): 383 / 318 / 253 CFM Sound Level (Hi/Med/Lo): 39 / 34 / 29 dB(A) Net Dimensions (WDH): 32 x 8-1/8 x 11-1/2 Inches Carton Dimensions (WDH): 34-7/8 x 11 x 14-3/8 Inches Net / Gross Weight: 19.8 / 26.5 lbs Outdoor Unit Data Part Number: YN012ALFI19RPE Breaker Needed: 20A (single-pole) Sound Level: 52 dB(A) Net Dimensions (WDH): 28-1/8 x 11-1/2 x 19-5/8 Inches Carton Dimensions (WDH): 33 x 13-1/4 x 21-5/8 Inches Net / Gross Weight: 55 / 66.1 lbs Manuals & Documents Technical Brochure User & Installation Manual Service Manual AHRI Certificate Energy Guide


Pioneer® Diamante Pro Series 9,000 BTU 19 SEER2 Ductless Mini-Split Air Conditioner Inverter+ Heat Pump Full Set 230V with 16 Ft. Kit

Overview Summary High Efficiency Diamante Pro Ductless Mini Split Heat Pump System Cooling capacity: 9,000 BTU/H with 19 SEER2 / 10 EER2 efficiency Heating capacity: 10,000 BTU/H with 8.5 HSPF2 / 3.41 COP2 efficiency Voltage: 208~230V, 60Hz, 1Ph High Wall Mounted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Low Ambient Unit (-13°F) AHRI Estimated Annual Operating Costs: Cooling: $63.00 Heating: $201.00 [[SERIES]] What's Included Indoor Unit Outdoor Unit Wireless Remote Control (with wall holder and batteries) 16 Ft. Copper Lines 16 Ft. Electrical Wire 10 Ft. Drain for indoor/outdoor Wall Passage Sleeve Putty for Wall Hole Leak Guard Sealer Wrapping Tape Installation Manual User’s Manual Our Guarantee 5 years Warranty for Parts 5 years Warranty for Compressor Features [[FEATURES]] Technical Information Performance Data Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 9,000 BTU/h Cooling Capacity Range: 2,700~9,900 BTU/h Cooling SEER2: 19.0 BTU/W.h Cooling EER2: 10.0 BTU/W.h Heating Rated Capacity: 10,000 BTU/h Heating Capacity Range: 3,000~11,000 BTU/h Heating HSPF2 (Region IV/V): 8.5 / 7.0 BTU/W.h Heating C.O.P.2 (47°F/5°F): 3.41 / 1.75 W/W Refrigerant Type: R410A Suitable Area: 100~350 Sq.F Indoor Unit Data Part Number: WT009GLFI19HLE Air Flow (Hi/Med/Lo): 353 / 288 / 250 CFM Sound Level (Hi/Med/Lo): 39 / 34 / 29 dB(A) Net Dimensions (WDH): 32 x 8-1/8 x 11-1/2 Inches Carton Dimensions (WDH): 34-7/8 x 11 x 14-3/8 Inches Net / Gross Weight: 19.8 / 26.5 lbs Outdoor Unit Data Part Number: YN009GLFI19RPE Breaker Needed: 15A (double-pole) Sound Level: 50 dB(A) Net Dimensions (WDH): 28-1/8 x 11-3/8 x 19-5/8 Inches Carton Dimensions (WDH): 33 x 13-3/8 x 21-5/8 Inches Net / Gross Weight: 48.5 / 57.3 lbs Manuals & Documents Technical Brochure User & Installation Manual Service Manual AHRI Certificate Energy Guide


Pioneer® Diamante Pro Series 12,000 BTU 19 SEER2 Ductless Mini-Split Air Conditioner Inverter+ Heat Pump Full Set 230V with 16 Ft. Kit

Overview Summary High Efficiency Diamante Pro Ductless Mini Split Heat Pump System Cooling capacity: 12,000 BTU/H with 19 SEER2 / 10 EER2 efficiency Heating capacity: 12,200 BTU/H with 8.5 HSPF / 3.21 COP2 efficiency Voltage: 208~230V, 60Hz, 1Ph High Wall Mounted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Low Ambient Unit (-13°F) AHRI Estimated Annual Operating Costs: Cooling: $83.00 Heating: $278.00 [[SERIES]] What's Included Indoor Unit Outdoor Unit Wireless Remote Control (with wall holder and batteries) 16 Ft. Copper Lines 16 Ft. Electrical Wire 10 Ft. Drain for indoor/outdoor Wall Passage Sleeve Putty for Wall Hole Leak Guard Sealer Wrapping Tape Installation Manual User’s Manual Our Guarantee 5 years Warranty for Parts 5 years for Compressor Features [[FEATURES]] Technical Information Performance Data Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 12,000 BTU/h Cooling Capacity Range: 3,600~13,200 BTU/h Cooling SEER2: 19.0 BTU/w Cooling EER2: 10.0 BTU/w Heating Rated Capacity: 12,500 BTU/h Heating Capacity Range: 3,6600~13,420 BTU/h Heating HSPF2 (Region IV/V): 8.5 / 7.2 BTU/W.h Heating C.O.P.2 (47°F/5°F): 3.21 / 1.75 W/W Refrigerant Type: R410A/34.2 oz. Suitable Area: 200~450 Sq.F Indoor Unit Data Part Number: WT012GLFI19HLE Air Flow (Hi/Med/Lo): 383 / 318 / 253 CFM Sound Level (Turbo/Hi/Med/Lo/Mute): 41 / 39 / 34 / 29 / 27 dB(A) Net Dimensions (WDH): 32 x 8-1/8 x 11-1/2 Inches Carton Dimensions (WDH): 34-7/8 x 11 x 14-3/8 Inches Net / Gross Weight: 19.8 / 24.2 Lbs Outdoor Unit Data Part Number: YN012GLFI19RPE Breaker Needed: 15A (double-pole) Sound Level: 51 dB(A) Net Dimensions (WDH): 28-1/8 x 11-3/8 x 19-5/8 Inches Carton Dimensions (WDH): 33 x 13-3/8 x 21-5/8 Inches Net / Gross Weight: 57.3 / 66.3 lbs Manuals & Documents Technical Brochure User & Installation Manual Service Manual AHRI Certificate Energy Guide


Pioneer® Diamante Pro Series 24,000 BTU 19 SEER2 Ductless Mini-Split Air Conditioner Inverter+ Heat Pump Full Set 230V with 16 Ft. Kit

Overview Summary High Efficiency Diamante Pro Ductless Mini Split Heat Pump System Cooling capacity: 24,000 BTU/H with 19 SEER2 / 10.0 EER2 efficiency Heating capacity: 24,400 BTU/H with 8.5 HSPF2 / 3.21 COP2 efficiency Voltage: 208~230V, 60Hz, 1Ph High Wall Mounted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Low Ambient Unit (-13°F) AHRI Estimated Annual Operating Costs: Cooling: $176.00 Heating: $516.00 [[SERIES]] What's Included Indoor Unit Outdoor Unit Wireless Remote Control (with wall holder and batteries) 16 Ft. Copper Lines 16 Ft. Electrical Wire 10 Ft. Drain for indoor/outdoor Wall Passage Sleeve Putty for Wall Hole Leak Guard Sealer Wrapping Tape Installation Manual User’s Manual Our Guarantee 5 years Warranty for Parts 5 years Warranty for Compressor Features [[FEATURES]] Technical Information Performance Data Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 24,000 BTU/h Cooling Capacity Range: 7,200~26,400 BTU/h Cooling SEER2: 19.0 BTU/W.h Cooling EER2: 10.0 BTU/W.h Heating Rated Capacity: 24,400 BTU/h Heating Capacity Range: 7320~26,840 BTU/h Heating HSPF2 (Region IV/V): 8.5 / 7.0 BTU/W.h Heating C.O.P.2 (47°F/5°F): 3.21 / 1.75 W/W Refrigerant Type: R410A/50.1 oz. Suitable Area: 550~1000 Sq.F Indoor Unit Data Part Number: WT024GLFI19HLE Air Flow (Hi/Med/Lo): 847 / 700 / 641 CFM Sound Level (Hi/Med/Lo): 48 / 43 / 38 dB(A) Net Dimensions (WDH): 46-5/8 x 10-1/4 x 13-3/8 Inches Carton Dimensions (WDH): 49-3/4 x 13-1/4 x 16-1/2 Inches Net / Gross Weight: 37.5 / 46.3 lbs Outdoor Unit Data Part Number: YN024GLFI19RPE Breaker Needed: 20A (double-pole) Sound Level: 58.0 dB(A) Net Dimensions (WDH): 33-1/4 x 15 x 27-1/2 Inches Carton Dimensions (WDH): 37-3/4 x 17 x 29-1/2 Inches Net / Gross Weight: 95.9 / 107.3 lbs Manuals & Documents Technical Brochure User & Installation Manual Service Manual AHRI Certificate Energy Guide


Wireless Internet Access & Control Module for Pioneer® Diamante Pro WYT/WT Series Systems

Summary Plugs into any Pioneer® Diamante Pro WYT/WT Model Ductless Split System. Compatible with any Pioneer® WYT/WT Model Ductless Split System (WYT-17, WYT-19, WYT-20) Free downloadable app for iOS or Android. Full programming and reporting interfaces. Consistently stable with reliable servers. Compatible with WYT systems only. For other models, see our wall module. For WYS models, see our WYS module. One module is needed per wall unit. Not for Diamante Ultra or Quantum Ultra or Hyperformance systems which come with WiFi included. Manuals & Downloads User Manual Installation Manual Pairing Instructions Installation Video Download iOS App Download Android App


Pioneer® 24,000 BTU 16.5 SEER2 Ducted Central Split Inverter+ Air Conditioner Heat Pump System, 2nd Generation

Overview Summary Ultra High Efficiency Inverter+ central ducted split heat pump system Cooling capacity: 22,000 BTU/H with 16.5 SEER2 / 10.1 EER2 efficiency Heating capacity: 26,000 BTU/H with 9 HSPF2 / 3.4 COP2 efficiency Voltage: 208~230 V, 60 Hertz, 1 Ph Central Ducted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Energy-Star Cold-Climate Certified Communicating system with dedicated signal transmission Includes 5 kW Electric Strip Heater AHRI Estimated Annual Operating Costs: Cooling: $176.00 Heating: $507.00 [[SERIES]] What's Included Indoor Unit (Downflow-capable, with TXV) Outdoor Unit (Side-Discharge, with filter drier) Electric Strip Heater (5 kW w/ breaker) Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 years compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 208~230V, 60Hz, 1Ph Max Cooling Rated Capacity (Min~Max): 22,000 (7,200~26,000) BTU/h Cooling SEER2: 16.5 BTU/W.h Cooling EER2: 10.1 BTU/W.h Max Heating Rated Capacity (Min~Max): 26,000 (8,900 ~ 26,000) BTU/h Heating HSPF2 (Region IV): 9.0 BTU/w Heating C.O.P.2 (47°F/5°F): 3.4 / 2.16 W/W Refrigerant Type: R-410a Suitable Area: 800 Sq.F Operating Temperatures: (-13°F - 75°F/Heating)/(5° - 122°F/Cooling) Indoor Unit Data Model: DR024GHFD18HT2 Air Flow: 800 CFM Sound Level: 55 dB(A) Fan Motor Type: Multi-Speed ECM Net Dimensions (WDH): 19-5/8 × 21-5/8 x 46-1/8 Inches Carton Dimensions (WDH): 22-1/2 × 25-3/8 × 49-5/8 Inches Net / Gross Weight: 136 / 159 Lbs Outdoor Unit Data Model: YH1824GHFD18R2 Sound Level: 54 dB(A) Metering Device: EXV Net Dimensions (WDH): 33-7/8 × 12-1/4 × 26-3/8 Inches Carton Dimensions (WDH): 39 × 17-3/4 × 28-3/4 Inches Net / Gross Weight: 112 / 121 Lbs Manuals & Downloads Series Technical Brochure Indoor Section Installation Manual Outdoor Section Installation Manual Indoor Section Service Manual Outdoor Section Service Manual DYR1824GMFI18R Submittal Sheet AHRI Certificate Energy Guide


Pioneer® 36,000 BTU 18 SEER2 Ducted Central Split Inverter+ Air Conditioner Heat Pump System, 2nd Generation

Overview Summary Ultra High Efficiency Inverter+ central ducted split heat pump system Cooling capacity: 33,000 BTU/H with 18.0 SEER2 / 10.1 EER2 efficiency Heating capacity: 38,000 BTU/H with 9.5 HSPF2 / 3.3 COP2 efficiency Voltage: 208~230 V, 60 Hertz, 1 Ph Central Ducted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Energy-Star Cold-Climate Certified Communicating system with dedicated signal transmission Includes 10 kW Electric Strip Heater w/ breaker AHRI Estimated Annual Operating Costs: Cooling: $264.00 Heating: $730.00 [[SERIES]] What's Included Indoor Unit (Downflow-capable, with TXV) Outdoor Unit (Side-Discharge, with filter drier) Electric Strip Heater (10 kW w/ breaker) Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 years compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 208~230V, 60Hz, 1Ph Max Cooling Rated Capacity (Min~Max): 33,000 (11,800~36,800) BTU/h Cooling SEER2: 18.0 BTU/W.h Cooling EER2: 10.1 BTU/W.h Max Heating Rated Capacity (Min~Max): 38,000 (8,900 ~ 38,200) BTU/h Heating HSPF2 (Region IV): 9.5 BTU/W.h Heating C.O.P.2 (47°F/5°F): 3.3 / 2.1 W/W Refrigerant Type: R410a Suitable Area: 1,200 Sq.F Operating Temperatures: (-13°F - 75°F/Heating)/(5° - 122°F/Cooling) Indoor Unit Data Model: DR036GHFD18HT2 Air Flow: 1120 CFM Sound Level: 57 dB(A) Fan Motor Type: Multi-Speed ECM Net Dimensions (WDH): 19-5/8 × 21-5/8 × 46-1/8 Inches Carton Dimensions (WDH): 22-1/2 × 25-3/8 × 49-5/8 Inches Net / Gross Weight: 140 / 163 Lbs Outdoor Unit Data Model: YH3036GHFD18R2 Sound Level: 57 dB(A) Metering Device: EXV Net Dimensions (WDH): 37-3/8 x 13-3/8 x 33 Inches Carton Dimensions (WDH): 43-3/4 x 18-1/8 x 36-1/4 Inches Net / Gross Weight: 148 / 159 Lbs Manuals & Downloads Series Technical Brochure Indoor Section Installation Manual Outdoor Section Installation Manual Indoor Section Service Manual Outdoor Section Service Manual DYR3036GMFI18R Submittal Sheet AHRI Certificate Energy Guide


Pioneer® 56,000 BTU 17 SEER2 Ducted Central Split Inverter+ Air Conditioner Heat Pump System, 2nd Generation

Overview Summary Ultra High Efficiency Inverter+ central ducted split heat pump system Cooling capacity: 56,000 BTU/H with 17 SEER2 / 8.25 EER2 efficiency Heating capacity: 56,000 BTU/H with 8.5 HSPF2 / 3.1 COP2 efficiency Voltage: 208~230 V, 60 Hertz, 1 Ph Central Ducted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Communicating system with dedicated signal transmission Includes Electric Strip Heater AHRI Estimated Annual Operating Costs: Cooling: $422.00 Heating: $1184.00 [[SERIES]] What's Included Indoor Unit (Downflow-capable, with TXV) Outdoor Unit (Side-Discharge, with filter drier) Electric Strip Heater (10 kW) Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 years compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 208~230V, 60Hz, 1Ph Max Cooling Rated Capacity (Min~Max): 56,000 (18,300~59,400) BTU/h Cooling SEER2: 17 BTU/W.h Cooling EER2: 8.25 BTU/W.h Max Heating Rated Capacity (Min~Max): 56,000 (17,600 ~ 57,500) BTU/h Heating HSPF2 (Region IV): 8.5 BTU/W.h Heating C.O.P.2 (47°F/5°F): 3.1 / 1.86 W/W Refrigerant Type: R410a Suitable Area: 2,000 Sq.F Indoor Unit Data Model: DR060GHFD18HT2 Air Flow: 1706 CFM Sound Level: 65 dB(A) Fan Motor Type: Multi-Speed ECM Net Dimensions (WDH): 22 × 24 × 53-7/8 Inches Carton Dimensions (WDH): 25-1/4 × 28 × 55-1/2 Inches Net / Gross Weight: 187 / 214 Lbs Outdoor Unit Data Model: YH4860GHFD18R2 Sound Level: 60 dB(A) Metering Device: EXV Net Dimensions (WDH): 37-3/8 × 13-3/8 × 54-1/2 Inches Carton Dimensions (WDH): 43-3/4 ×18-1/8 × 60-1/4 Inches Net / Gross Weight: 251 / 278 Lbs Manuals & Downloads Series Technical Brochure Indoor Section Installation Manual Outdoor Section Installation Manual Indoor Section Service Manual Outdoor Section Service Manual DYR4860GMFI18R Submittal Sheet AHRI Certificate Energy Guide


UVC Bacterial Disinfection Kit for Mini Split Systems

Overview Summary UVC MINI KITS are an innovative application of UV disinfection in Mini Splits and other space-limited systems. Prevents bio-growth & related odors on fan, coil and other interior surfaces! Applicable for These Air System Types: Wall-Mount Cassette Floor-Ceiling Benefits Prevent mold and bacteria growth Ensure a clean mini-split system Extend life of a mini split system Improve indoor air quality Reduce maintenance cost Features Super compact / High intensity Easy fit with simple installation 85-265 VAC wide range power supply Cut-to-length LED strip design Water resistance / Heat dissipation 50,000 hours+ expected LED life Three years system warranty Designed to fit major brands For Wall-Mount, Floor-Ceiling & Cassette Kits Include: LED Strip (UVA/UVC) LED Driver Strip Cabinet Bushing Block 3M Sticker Hardware User Manual Cleaning Cloth Manuals & Downloads Owner's Manual


Replacement Remote Control for (WYT/WT) Models - Gen 1

Overview Spare or replacement remote control for all Pioneer Diamante Pro/Essenza/Ultra Split Systems as well as Quantum Ultra 2025 and Quantum Hyperformance 2025 models (Indoor Unit model number starts with "WT", "CT", "UT", or "RT"). LCD screen infrared remote transmitter. All generation remotes are cross-compatible, only physical shape and some specific features may remain limited to a particular remote controller. Manuals & Downloads Remote User Manual


Pioneer Official Store Gift Card - $250.00

Shopping for someone else but not sure what to give them? Give them the gift of choice with a Pioneer gift card. Gift cards are delivered by email and contains instructions to redeem them at checkout. Our gift cards have no additional processing fees. This digital gift card should be used only for any purchase on https://www.pioneerminisplit.com This gift card has no expiration date.


Pioneer Official Store Gift Card - $500.00


Pioneer Official Store Gift Card - $1,000.00


Pioneer® 48,000 BTU Ducted Central Split Inverter+ Air Handler Unit Inside Section 230V

Overview Summary Air Handler Unit indoor section of DYR4248GMFI18R set series. This is not a full system, only the partial section of a complete set! Highlights Compatible with any standard 24V wall thermostat Universal match for all AC heat pumps of matching capacity Dual electric racks accept 5, 7.5, and 10kW electric heaters Multi-position, field convertible (vertical, horizontal, downflow) Outdoor Unit Data Model: DR048GHFD18HT2 Sound Level: 64 dB(A) Throttle Type: TXV Net Dimensions (WDH): 22 x 24 x 53-7/8 Inches Carton Dimensions (WDH): 25-1/4 x 28 x 55-1/2 Inches Net / Gross Weight: 187.2 / 214 Lbs Manuals & Downloads Series Technical Brochure Indoor Section Installation Manual Indoor Section Service Manual


Pioneer® 48,000 BTU 17.5 SEER2 Ducted Central Split Inverter+ Condenser AC Heat Pump Outside Section 230V

Overview Summary Outdoor unit section of DYR4248GMFI18R set series. This is not a full system, only the partial section of a complete set! Outdoor Unit Data Model: YH4248GHFD18R2 Sound Level: 59 dB(A) Metering Device: EXV Net Dimensions (WDH): 37-3/8 x 13-3/8 x 54-5/8 Inches Carton Dimensions (WDH): 43-3/4 x 18-1/8 x 60-1/4 Inches Net / Gross Weight: 227 / 254 Lbs Manuals & Downloads Series Technical Brochure Outdoor Section Installation Manual Outdoor Section Service Manual


Pioneer® 12,000 BTU 20.8 SEER2 Ductless Mini-Split Inverter+ Air Conditioner Heat Pump System Full Set 115V - 50 Ft

Overview Summary High Efficiency Quantum Series Inverter+ ductless mini split heat pump system Cooling capacity: 12,000 BTU/H with 20.8 SEER2 / 10.3 EER2 efficiency Heating capacity: 12,000 BTU/H with 8.7 HSPF2 / 3.13 COP2 efficiency Voltage: 110~120V, 60Hz, 1Ph High Wall Mounted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Customizable length copper line set with flare connections AHRI Estimated Annual Operating Costs: Cooling: $79.00 Heating: $242.00 [[SERIES]] What's Included Indoor Unit Outdoor Unit Wireless Remote Control Various Installation Kit Options Available Flare Connection Leak Guard Sealer Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 year compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 110~120V, 60Hz, 1Ph Cooling Rated Capacity: 12,000 BTU/h Cooling Capacity Range: 4,300~12,600 BTU/h Cooling SEER2: 20.8 BTU/W.h Cooling EER2: 10.3 BTU/W.h Heating Rated Capacity: 12,000 BTU/h Heating Capacity Range: 4,000~12,500 BTU/h Heating HSPF2 (Region IV/V): 8.7 / 6.6 BTU/W.h Heating C.O.P.2 (47°F/5°F): 3.13 / 1.91 W/W Refrigerant Type: R410A/30 Suitable Area: 300~450 Sq.F Indoor Unit Data Part Number: WS012AMFI20HLD Air Flow (Turbo/Hi/Med/Lo): 341 / 309 / 206 / 176 CFM Sound Level (Hi/Med/Lo): 41.5 / 30.5 / 26.0 dB(A) Net Dimensions (WDH): 31.57 x 7.44 x 11.69 Inches Carton Dimensions (WDH): 34.45 x 11.22 x 14.96 Inches Net / Gross Weight: 20 / 25 lbs Outdoor Unit Data Model Number: YN012AMFI20RPD Sound Level: 55.5 dB(A) Net Dimensions (WDH): 30.1 x 11.93 x 21.85 Inches Carton Dimensions (WDH): 34.8 x 13.25 x 24 Inches Net / Gross Weight: 62.2 / 67.7 lbs Breaker Needed: 20A (single-pole) Manuals & Downloads Technical Brochure User Manual Installation Manual Service Manual Disassembly Guide AHRI Certificate Energy Guide


Pioneer® 12,000 BTU 21.4 SEER2 Ductless Mini-Split Inverter+ Air Conditioner Heat Pump System Full Set 230V - 25 Ft

Overview Summary High Efficiency Quantum Series Inverter+ ductless mini split heat pump system Cooling capacity: 12,000 BTU/H with 21.4 SEER2 / 10.8 EER2 efficiency Heating capacity: 12,000 BTU/H with 9.1 HSPF2 / 3.23 COP2 efficiency Voltage: 208~230V, 60Hz, 1Ph High Wall Mounted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Customizable length copper line set with flare connections AHRI Estimated Annual Operating Costs: Cooling: $77.00 Heating: $254.00 [[SERIES]] What's Included Indoor Unit Outdoor Unit Wireless Remote Control Various Installation Kit Options Available Flare Connection Leak Guard Sealer Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 year compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 12,000 BTU/h Cooling Capacity Range: 3,800~12,850 BTU/h Cooling SEER2: 21.40 BTU/W.h Cooling EER2: 10.80 BTU/W.h Heating Rated Capacity: 12,000 BTU/h Heating Capacity Range: 2,730~12,500 BTU/h Heating HSPF2 (Region IV/V): 9.1 / 6.9 BTU/W.h Heating C.O.P.2 (47°F/5°F): 3.23 / 1.68 W/W Refrigerant Type: R410A/28.6 oz. Suitable Area: 250~450 Sq.F Indoor Unit Data Part Number: WS012GMFI20HLD Air Flow (Hi/Med/Lo): 317 / 207 / 144 CFM Sound Level (Hi/Med/Lo): 37 / 30 / 22.5 dB(A) Net Dimensions (WDH): 31"-1/2 x 7"-3/8 x 11"-5/8 Inches Carton Dimensions (WDH): 34"-1/2 x 11"-1/4 x 15" Inches Net / Gross Weight: 19.8 / 25 Lbs Outdoor Unit Data Part Number: YN012GMFI20RPD Sound Level: 55.5 dB(A) Net Dimensions (WDH): 30"-1/8 x 11"-7/8 x 21"-7/8 Inches Carton Dimensions (WDH): 34"-7/8 x 13"-1/4 x 24" Inches Net / Gross Weight: 59.3 / 64.8 lbs Breaker Needed: 15A (double-pole) Manuals & Downloads Technical Brochure User Manual Installation Manual Service Manual Disassembly Guide AHRI Certificate Energy Guide


Pioneer® 12,000 BTU 21.4 SEER2 Ductless Mini-Split Inverter+ Air Conditioner Heat Pump System Full Set 230V - 33 Ft


Pioneer® 18,000 BTU 19 SEER2 Ductless Mini-Split Inverter+ Air Conditioner Heat Pump System Full Set 230V - 10 Ft

Overview Summary High Efficiency Quantum Series Inverter+ ductless mini split heat pump system inverter and air conditioner heat pump system full set Cooling capacity: 18,000 BTU/H with 19 SEER2 / 10.5 EER2 efficiency Heating capacity: 18,800 BTU/H with 8.7 HSPF2 / 2.93 COP2 efficiency Voltage: 208~230V, 60Hz, 1Ph High Wall Mounted Air Conditioning & Heating System Variable Speed DC high-efficiency Inverter Operation Mode Customizable length copper line set with flare connections AHRI Estimated Annual Operating Costs: Cooling: $125.00 Heating: $397.00 [[SERIES]] What's Included Indoor Unit Outdoor Unit Wireless Remote Control Various Installation Kit Options Available Flare Connection Leak Guard Sealer Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 year compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 18,000 BTU/h Cooling Capacity Range: 3,900~20,000 BTU/h Cooling SEER2: 19 BTU/W.h Cooling EER2: 10.5 BTU /W.h Heating Rated Capacity: 18,800 BTU/h Heating Capacity Range: 6,300~19,400 BTU/h Heating HSPF2 (Region IV/V): 8.7 / 6.8 BTU/W.h Heating C.O.P.2 (47°F/5°F): 2.93 / 2.1 W/W Refrigerant Type: R410A/47.6 oz. Suitable Area: 400~650 Sq.F Indoor Unit Data Model Number: WS018GMFI20HLD Air Flow (Hi/Med/Lo): 388 / 259 / 218 CFM Sound Level (Hi/Med/Lo): 43.5 / 34.5 / 30.0 dB(A) Net Dimensions (WDH): 38" x 8"-1/2 x 12"-1/2 Carton Dimensions (WDH): 41"-1/8 x 12" x 16"-1/8 Net / Gross Weight: 23.8 / 31.5 lbs Outdoor Unit Data Model Number: YN018GMFI20RPD Sound Level: 57 dB(A) Net Dimensions (WDH): 31"-5/8 x 13" x 21"-7/8 Carton Dimensions (WDH): 36" x 14"-5/8 x 24"-1/4 Net / Gross Weight: 73.9 / 79.8 lbs Breaker Needed: 20A (double-pole) Manuals & Downloads Technical Brochure User Manual Installation Manual Service Manual Disassembly Guide AHRI Certificate Energy Guide


Pioneer® 30,000 BTU 18.6 SEER2 Ductless Mini-Split Inverter+ Air Conditioner Heat Pump System Full Set 230V - 10 Ft

Overview Summary High Efficiency Quantum Series Inverter+ ductless mini split heat pump system Cooling capacity: 30,000 BTU/H with 18.6 SEER2 / 10.5 EER2 efficiency Heating capacity: 30,000 BTU/H with 8.7 HSPF2 / 2.71 COP2 efficiency Voltage: 208~230V, 60Hz, 1Ph High Wall Mounted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Customizable length copper line set with flare connections AHRI Estimated Annual Operating Costs: Cooling: $213.00 Heating: $668.00 [[SERIES]] What's Included Ductless Wall-Type Indoor Air Handler Unit Outdoor Heat Pump Condensing Unit Wireless Handheld Remote Control Various Installation Kit Options Available Flare Connection Leak Guard Sealer Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 year compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 30,000 BTU/h Cooling Capacity Range: 7,200~31,600 BTU/h Cooling SEER2: 18.6 BTU/W.h Cooling EER2: 10.5 BTU/W.h Heating Rated Capacity: 30,000 BTU/h Heating Capacity Range: 10,600~32,500 BTU/h Heating HSPF2 (Region IV/V): 8.7 / 6.8 BTU/W.h Heating C.O.P.2 (47°F/5°F): 2.71 / 1.84 W/W Refrigerant Type: R410A/97 Suitable Area: 800~1,100 Sq.F Indoor Unit Data Model Number: WS030GMFI20HLD Air Flow (Hi/Med/Lo): 974 / 618 / 471 CFM Sound Level (Hi/Lo): 51.5 / 44 dB(A) Net Dimensions (WDH): 49.5 x 11.2 x 14.3 Inches Carton Dimensions (WDH): 52.7 x 17.7 x 15.0 Inches Net / Gross Weight: 37.5 / 50.5 lbs Outdoor Unit Data Model Number: YN030GMFI20RPD Sound Level: 60.0 dB(A) Breaker Needed: 30A (double-pole) Net Dimensions (WDH): 37.3 x 16.5 x 31.8 Inches Carton Dimensions (WDH): 42.8 x 19.6 x 34.0 Inches Net / Gross Weight: 141.7 / 151.9 lbs Manuals & Downloads Technical Brochure User Manual Installation Manual Service Manual Disassembly Guide AHRI Certificate Energy Guide


Pioneer® 30,000 BTU 18.6 SEER2 Ductless Mini-Split Inverter+ Air Conditioner Heat Pump System Full Set 230V - WITHOUT INSTALLATION KIT


Pioneer® 36,000 BTU 17.5 SEER2 Ductless Mini-Split Inverter+ Air Conditioner Heat Pump System Full Set 230V - 50 Ft

Overview Summary High Efficiency Quantum Series Inverter+ ductless mini split heat pump system Cooling capacity: 36,000 BTU/H with 17.5 SEER2 / 8.5 EER2 efficiency Heating capacity: 36,000 BTU/H with 8.7 HSPF2 / 2.47 COP2 efficiency Voltage: 208~230V, 60Hz, 1Ph High Wall Mounted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Customizable length copper line set with flare connections AHRI Estimated Annual Operating Costs: Cooling: $272.00 Heating: $645.00 [[SERIES]] What's Included Ductless Wall-Type Indoor Air Handler Unit Outdoor Heat Pump Condensing Unit Wireless Handheld Remote Control Various Installation Kit Options Available Flare Connection Leak Guard Sealer Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 year compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 36,000 BTU/h (3-Ton) Cooling Capacity Range: 8,900~36,300 BTU/h Cooling SEER2: 17.5 BTU/W.h Cooling EER2: 8.5 BTU/W.h Heating Rated Capacity: 36,000 BTU/h (3-Ton) Heating Capacity Range: 11,400~37,800 BTU/h Heating HSPF2 (Region IV/V): 8.7 / 6.8 BTU/W.h Heating C.O.P.2 (47°F/5°F): 2.47 / 1.97 W/W Refrigerant Type: R410A/120 Suitable Area: 900~1,250 Sq.F Indoor Unit Data Model Number: WS036GMFI20HLD Air Flow (Turbo/Hi/Med/Lo): 882 / 732 / 518 / 400 CFM Sound Level (Hi/Med/Lo): 56.5 / 54.5 / 40 dB(A) Net Dimensions (WDH): 49"-1/2 x 11"-1/8 x 14"-1/4 Inches Carton Dimensions (WDH): 52"-3/4 x 17"-3/4 x 15"-1/4 Inches Net / Gross Weight: 40 / 52.5 lbs Outdoor Unit Data Model Number: YN036GMFI20RPD Sound Level: 63.5 dB(A) Breaker Needed: 30A (double-pole) Net Dimensions (WDH): 37"-1/4 x 16"-1/4 x 31"-7/8 Inches Carton Dimensions (WDH): 42"-7/8 x 19"-5/8 x 34" Inches Net / Gross Weight: 150 / 159 lbs Manuals & Downloads Technical Brochure User Manual Installation Manual Service Manual Disassembly Guide AHRI Certificate Energy Guide


Pioneer® 9,000 BTU 21.7 SEER2 Ductless Mini-Split Inverter+ Energy-Star Air Conditioner Heat Pump System Full Set 230V - 50 Ft

Overview Summary High Efficiency Quantum Series Inverter+ ductless mini split heat pump system Cooling capacity: 9,000 BTU/H with 21.7 SEER2 / 12.6 EER2 efficiency Heating capacity: 10,000 BTU/H with 9.1 HSPF2 / 3.29 COP2 efficiency Voltage: 208~230V, 60Hz, 1Ph High Wall Mounted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Customizable length copper line set with flare connections Energy-Star Certified AHRI Estimated Annual Operating Costs: Cooling: $55.00 Heating: $211.00 [[SERIES]] What's Included Indoor Unit Outdoor Unit Wireless Remote Control Various Ductless Mini Split Installation Kit Options Available Flare Connection Leak Guard Sealer Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 year compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 9,000 BTU/h Cooling Capacity Range: 2,900~10,200 BTU/h Cooling SEER2: 21.7 BTU/W.h Cooling EER2: 12.6 BTU/W.h Heating Rated Capacity: 10,000 BTU/h Heating Capacity Range: 2,400~10,900 BTU/h Heating HSPF2 (Region IV/V): 9.1 / 6.9 BTU/W.h Heating C.O.P.2 (47°F/5°F): 3.29 / 1.96 W/W Refrigerant Type: R410A Suitable Area: 100~350 Sq.F Indoor Unit Data Model Number: WS009GMFI20HLD Air Flow (Hi/Med/Lo): 259 / 193 / 136 CFM Sound Level (Hi/Med/Lo): 40.5 / 30.5 / 24 dB(A) Net Dimensions (WDH): 28.5 x 7.3 x 11.4 Inches Carton Dimensions (WDH): 31.2 x 10.6 x 14.75 Inches Net / Gross Weight: 17 / 22.3 lbs Outdoor Unit Data Model Number: YN009GMFI20RPD Sound Level: 53 dB(A) Breaker Needed: 15A (double-pole) Net Dimensions (WDH): 31.3 x 10.6 x 21.8 Inches Carton Dimensions (WDH): 34.8 x 13.2 x 24 Inches Net / Gross Weight: 55.1 / 60.9 lbs Manuals & Downloads Technical Brochure User Manual Installation Manual Service Manual Disassembly Guide AHRI Certificate Energy Guide


Pioneer® 9,000 BTU 21.7 SEER2 Ductless Mini-Split Inverter+ Energy-Star Air Conditioner Heat Pump System Full Set 230V - WITHOUT INSTALLATION KIT


Pioneer® 9,000 BTU 21.5 SEER2 Ductless Mini-Split Inverter+ Energy-Star Air Conditioner Heat Pump System Full Set 115V - 10 Ft

Overview Summary High Efficiency Quantum Series Inverter+ ductless mini split heat pump system Cooling capacity: 9,000 BTU/H with 21.5 SEER2 / 12.5 EER2 efficiency Heating capacity: 10,000 BTU/H with 9.0 HSPF2 / 2.93 COP2 efficiency Voltage: 110~120V, 60Hz, 1Ph High Wall Mounted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Customizable length copper line set with flare connections Energy-Star Certified AHRI Estimated Annual Operating Costs: Cooling: $58.00 Heating: $211.00 [[SERIES]] What's included with the Pioneer 9,000 BTU 20.5 SEER 115V ductless mini-split inverter and air conditioner heat pump system full set: Indoor Unit Outdoor Unit Wireless Remote Control Various Installation Kit Options Available Flare Connection Leak Guard Sealer Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 year compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 110~120V, 60Hz, 1Ph Cooling Rated Capacity: 9,000 BTU/h Cooling Capacity Range: 2,650~10,300 BTU/h Cooling SEER2: 21.5 BTU/W.h Cooling EER2: 12.5 BTU/W.h Heating Rated Capacity: 10,000 BTU/h Heating Capacity Range: 2,700~10,300 BTU/h Heating HSPF2 (Region IV/V): 9.0 / 6.9 BTU/W.h Heating C.O.P.2 (47°F/5°F): 2.93 / 1.89 W/W Refrigerant Type: R410A Suitable Area: 100~350 Sq.F Indoor Unit Data Part Number: WS009AMFI20HLD Air Flow (Hi/Med/Lo): 247 / 182 / 129 CFM Sound Level (Hi/Med/Lo): 38 / 32 / 25 dB(A) Net Dimensions (WDH): 28.43 x 7.36 x 11.42 Inches Carton Dimensions (WDH): 31.1 x 10.63 x 14.76 Inches Net / Gross Weight: 17.0 / 22.3 lbs Outdoor Unit Data Part Number: YN009AMFI20RPD Sound Level: 54.0 dB(A) Breaker Needed: 20A Single-Pole Net Dimensions (WDH): 30.2 x 11.8 x 21.8 Inches Carton Dimensions (WDH): 34.8 x 13.2 x 24 Inches Net / Gross Weight: 57.8 / 63.5 lbs Manuals & Downloads Technical Brochure User Manual Installation Manual Service Manual Disassembly Guide AHRI Certificate Energy Guide


Pioneer® EStar™ 12,000 BTU 22.7 SEER2 Ductless Mini-Split Inverter++ Energy-Star Air Conditioner Heat Pump System Full Set 115V - 10 Ft

Overview Summary Ultra High Efficiency Inverter++ ductless mini split heat pump system Cooling capacity: 12,000 BTU/H with 22.7 SEER2 / 12.5 EER2 efficiency Heating capacity: 12,000 BTU/H with 10.0 HSPF2 / 3.38 COP2 efficiency Voltage: 110~120 V, 60 Hertz, 1Ph High Wall Mounted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Customizable length copper line set with flare connections Energy-Star Certified AHRI Estimated Annual Operating Costs: Cooling: $74.00 Heating: $221.00 [[SERIES]] What's Included Indoor Unit Outdoor Unit Wireless Remote Control Various Installation Kit Options Available Flare Connection Leak Guard Sealer Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 year compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 110~120V, 60Hz, 1Ph Cooling Rated Capacity: 12,000 BTU/h Cooling Capacity Range: 3,500~12,150 BTU/h Cooling SEER2: 22.7 BTU/W.h Cooling EER2: 12.5 BTU/W.h Heating Rated Capacity: 12,000 BTU/h Heating Capacity Range: 4,600~12,904 BTU/h Heating HSPF2 (Region IV/V): 10.0 / 7.6 BTU/W.h Heating C.O.P.2 (47°F/5°F): 3.38 / 2.00 W/W Refrigerant Type: R410a Suitable Area: 200~450 Sq.F Indoor Unit Data Model Number: WS012AMFI22HLE Air Flow (Hi/Med/Lo): 306 / 212 / 147 CFM Sound Level (Hi/Lo): 36.0 / 23.0 dB(A) Net Dimensions (WDH): 31.5 x 7.3 x 11.6 Inches Carton Dimensions (WDH): 34.5 x 11.25 x 15 Inches Net / Gross Weight: 24 / 34.2 Lbs Outdoor Unit Data Model Number: YN012AMFI22RPE Sound Level: 52.5 dB(A) Breaker Needed: 20A (single-pole) Net Dimensions (WDH): 30.2 x 11.8 x 21.7 Inches Carton Dimensions (WDH): 34.8 x 13.25 x 24 Inches Net / Gross Weight: 66.8 / 72.3 Lbs Manuals & Downloads Series Technical Brochure Series User Manual Series Installation Manual Series Service Manual Disassembly Guide AHRI Certificate Energy Guide


Pioneer® EStar™ 12,000 BTU 22.7 SEER2 Ductless Mini-Split Inverter++ Energy-Star Air Conditioner Heat Pump System Full Set 115V - 33 Ft


Pioneer® EStar™ 12,000 BTU 22.7 SEER2 Ductless Mini-Split Inverter++ Energy-Star Air Conditioner Heat Pump System Full Set 115V - WITHOUT INSTALLATION


Pioneer® EStar™ 12,000 BTU 23.1 SEER2 Ductless Mini-Split Inverter++ Energy-Star Air Conditioner Heat Pump System Full Set 230V - 25 Ft

Overview Summary Ultra-High Efficiency Inverter++ ductless mini split heat pump system Cooling capacity: 12,000 BTU/H with 23.1 SEER2 / 12.5 EER2 efficiency Heating capacity: 12,000 BTU/H with 9.3 HSPF2 / 3.5 COP2 efficiency Voltage: 208~230 V, 60 Hertz, 1Ph High Wall Mounted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Customizable length copper line set with flare connections Energy-Star Certified AHRI Estimated Annual Operating Costs: Cooling: $72.00 Heating: $235.00 [[SERIES]] What's Included Indoor Unit Outdoor Unit Wireless Remote Control Various Installation Kit Options Available Flare Connection Leak Guard Sealer Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 year compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 12,000 BTU/h Cooling Capacity Range: 3,536~12,931 BTU/h Cooling SEER2: 23.1 BTU/w Cooling EER2: 12.5 BTU/w Heating Rated Capacity: 12,000 BTU/h Heating Capacity Range: 3,747~12,550 BTU/h Heating HSPF2 (Region IV/V): 9.3 / 7.1 BTU/W.h Heating C.O.P.2 (47°F/5°F): 3.50 / 2.24 W/W Refrigerant Type: R410a Suitable Area: 200~450 Sq.F Indoor Unit Data Part Number: WS012GMFI22HLE Air Flow (Turbo/Hi/Med/Lo): 323 / 306 / 212 / 147 CFM Sound Level (Hi/Med/Lo): 37.5 / 30.0 / 21.5 dB(A) Net Dimensions (WDH): 31"-1/2 x 7"-3/8 x 11"-5/8 Carton Dimensions (WDH): 34"1/2 x 11"-1/4 x 15" Net / Gross Weight: 19 / 24 Lbs Outdoor Unit Data Part Number: YN012GMFI22RPE Sound Level: 53.5 dB(A) Breaker Needed: 15A (double-pole) Net Dimensions (WDH): 30"-1/8 x 11"-7/8 x 21"-7/8 Carton Dimensions (WDH): 34"-7/8 x 13"-1/4 x 24" Net / Gross Weight: 63.7 / 69 Lbs Manuals & Downloads Series Technical Brochure Series User Manual Series Installation Manual Series Service Manual Disassembly Guide AHRI Certificate Energy Guide


Pioneer® EStar™ 12,000 BTU 23.1 SEER2 Ductless Mini-Split Inverter++ Energy-Star Air Conditioner Heat Pump System Full Set 230V - 33 Ft


Pioneer® EStar™ 18,000 BTU 23.7 SEER2 Ductless Mini-Split Inverter++ Energy-Star Air Conditioner Heat Pump System Full Set 230V - 10 Ft

Overview Summary Ultra High Efficiency Inverter++ ductless mini split heat pump system Cooling capacity: 18,000 BTU/H with 23.7 SEER2 / 13.5 EER2 efficiency Heating capacity: 18,000 BTU/H with 10.3 HSPF2 / 3.74 COP2 efficiency Voltage: 208~230 V, 60 Hertz, 1Ph High Wall Mounted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Customizable length copper line set with flare connections Energy-Star Certified AHRI Estimated Annual Operating Costs: Cooling: $110.00 Heating: $366.00 [[SERIES]] What's Included Indoor Unit Outdoor Unit Wireless Remote Control Various Installation Kit Options Available Flare Connection Leak Guard Sealer Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 year compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 18,000 BTU/h Cooling Capacity Range: 9,935~20,000 BTU/h Cooling SEER2: 23.7 BTU/W.h Cooling EER2: 13.5 BTU/W.h Heating Rated Capacity: 18,000 BTU/h Heating Capacity Range: 6,615~21,000 BTU/h Heating HSPF2 (Region IV/V): 10.3 / 7.6 BTU/W.h Heating C.O.P.2 (47°F/5°F): 3.74 / 2.39 W/W Refrigerant Type: R410a/56.4 oz. Suitable Area: 400~650 Sq.F Indoor Unit Data Model Number: WS018GMFI22HLE Air Flow (Turbo/Hi/Med/Lo): 706 / 470 / 353 / 294 CFM Sound Level (Hi/Med/Lo): 43 / 35 / 30 dB(A) Net Dimensions (WDH): 42.5 x 8.9 x 13.2 Inches Carton Dimensions (WDH): 45.5 x 12.6 x 16.3 Inches Net / Gross Weight: 29.5 / 37.5 Lbs Outdoor Unit Data Model Number: YN018GMFI22RPE Sound Level: 59.0 dB(A) Electrical Circuit Size: 20A (double-pole) Net Dimensions (WDH): 35 x 13.5 x 26.5 Inches Carton Dimensions (WDH): 39.2 x 15.7 x 29.1 Inches Net / Gross Weight: 94.5 / 101 Lbs Manuals & Downloads Series Technical Brochure Series User Manual Series Installation Manual Series Service Manual Disassembly Guide AHRI Certificate Energy Guide


Pioneer® EStar™ 18,000 BTU 23.7 SEER2 Ductless Mini-Split Inverter++ Energy-Star Air Conditioner Heat Pump System Full Set 230V - 25 Ft


Pioneer® EStar™ 18,000 BTU 23.7 SEER2 Ductless Mini-Split Inverter++ Energy-Star Air Conditioner Heat Pump System Full Set 230V - 33 Ft


Pioneer® EStar™ 18,000 BTU 23.7 SEER2 Ductless Mini-Split Inverter++ Energy-Star Air Conditioner Heat Pump System Full Set 230V - 50 Ft


Pioneer® EStar™ 18,000 BTU 23.7 SEER2 Ductless Mini-Split Inverter++ Energy-Star Air Conditioner Heat Pump System Full Set 230V - WITHOUT INSTALLATION


Pioneer® EStar™ 9,000 BTU 22.7 SEER2 Ductless Mini-Split Inverter++ Energy-Star Air Conditioner Heat Pump System Full Set 115V - 50 Ft

Overview Summary Ultra High Efficiency Inverter++ ductless mini split heat pump system Cooling capacity: 9,000 BTU/H with 22.7 SEER2 / 12.5 EER2 efficiency Heating capacity: 9,000 BTU/H with 10.0 HSPF2 / 3.86 COP2 efficiency Voltage: 110~120 V, 60 Hertz, 1 Ph High Wall Mounted Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Customizable length copper line set with flare connections Energy-Star Certified AHRI Estimated Annual Operating Costs: Cooling: $74.00 Heating: $221.00 [[SERIES]] What's Included Indoor Unit Outdoor Unit Wireless Remote Control Various Installation Kit Options Available Flare Connection Leak Guard Sealer Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 year compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 110~120V, 60Hz, 1Ph Cooling Rated Capacity: 9,000 BTU/h Cooling Capacity Range: 3,500~12,150 BTU/h Cooling SEER2: 22.7 BTU/W.h Cooling EER2: 12.5 BTU/W.h Heating Rated Capacity: 9,000 BTU/h Heating Capacity Range: 4,600~12,904 BTU/h Heating HSPF2 (Region IV/V): 10.0 / 7.6 BTU/W.h Heating C.O.P.2 (47°F/5°F): 3.86 / 2.00 W/W Refrigerant Type: R410a Suitable Area: 250~350 Sq.F Indoor Unit Data Part Number: WS009AMFI22HLE Air Flow (Hi/Med/Lo): 294 / 212 / 147 CFM Sound Level (Hi/Lo): 37.5 / 23.0 dB(A) Net Dimensions (WDH): 31.5 x 7.3 x 11.6 Inches Carton Dimensions (WDH): 34.5 x 11.2 x 14.7 Inches Net / Gross Weight: 18 / 22 Lbs Outdoor Unit Data Part Number: YN009AMFI22RPE Sound Level: 52.5 dB(A) Net Dimensions (WDH): 31.3 x 11.8 x 21.8 Inches Carton Dimensions (WDH): 35.3 x 13.6 x 14.6 Inches Net / Gross Weight: 64 / 69 Lbs Breaker Needed: 20A (single-pole) Manuals & Downloads Series Technical Brochure Series User Manual Series Installation Manual Series Service Manual Disassembly Guide AHRI Certificate Energy Guide


Pioneer® EStar™ 9,000 BTU 22.7 SEER2 Ductless Mini-Split Inverter++ Energy-Star Air Conditioner Heat Pump System Full Set 115V - WITHOUT INSTALLATION


Pioneer® 12,000 BTU 22.7 SEER2 Floor Console Mini-Split Inverter++ Energy-Star Air Conditioner Heat Pump System Full Set 230V - 25 Ft

Overview Summary Ultra High Efficiency Inverter++ floor console split heat pump system Cooling capacity: 12,000 BTU/H with 22.7 SEER2 / 13.0 EER2 efficiency Heating capacity: 12,000 BTU/H with 10.2 HSPF2 / 3.52 COP efficiency Voltage: 208~230 V, 60 Hertz, 1 Ph Floor Console Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Customizable length copper line set with flare connections Energy-Star Certified AHRI Estimated Annual Operating Costs: Cooling: $74.00 Heating: $254.00 [[SERIES]] What's Included Indoor Unit Outdoor Unit Wireless Remote Control Various Installation Kit Options Available Flare Connection Leak Guard Sealer Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 year compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 12,000 BTU/h Cooling Capacity Range: 2,850~13,000 BTU/h Cooling SEER2: 22.7 BTU/W.hr Cooling EER2: 13.0 BTU/W.hr Heating Rated Capacity: 12,000 BTU/h Heating Capacity Range: 2,250~14,800 BTU/h Heating HSPF: 10.0 BTU/w Refrigerant Type: R410a Suitable Area: 200~450 Sq.F Indoor Unit Data Model Number: FB012GMFILDFHE Air Flow (Hi/Med/Lo): 365 / 318 / 248 CFM Sound Level (Hi/Med/Lo): 43.0 / 39.0 / 33.0 dB(A) Net Dimensions (WDH): 31-1/4 x 7-7/8 x 24-1/2 Inches Carton Dimensions (WDH): 34 x 11 x 28-1/4 Inches Net / Gross Weight: 32.8 / 41.5 Lbs Outdoor Unit Data Model Number: YN012GMFI22RPE Sound Level: 53.5 dB(A) Breaker Needed: 15A (double-pole) Expansion Device Type: EXV Net Dimensions (WDH): 30-1/8 x 11-7/8 x 21-7/8 Inches Carton Dimensions (WDH): 34-7/8 x 13-1/4 x 24 Inches Net / Gross Weight: 63.7 / 69 Lbs Manuals & Downloads Series Technical Brochure Series User Manual Series Installation Manual Series Service Manual AHRI Certificate Energy Guide


Pioneer® 12,000 BTU 22.7 SEER2 Floor Console Mini-Split Inverter++ Energy-Star Air Conditioner Heat Pump System Full Set 230V - 50 Ft


Pioneer® 12,000 BTU 22.7 SEER2 Floor Console Mini-Split Inverter++ Energy-Star Air Conditioner Heat Pump System Full Set 230V - WITHOUT INSTALLATION K


Pioneer® 12,000 BTU 21.5 SEER 115V SEER 8-Way Compact Cassette Mini-Split Air Conditioner Heat Pump System Full Set - 10 Ft

Overview Summary Ultra High Efficiency Inverter++ ceiling cassette split heat pump system Cooling capacity: 12,000 BTU/H with 21.5 SEER efficiency Heating capacity: 12,000 BTU/H with 10.5 HSPF efficiency Voltage: 110~120V, 60 Hertz, 1 Ph Ceiling Compact Cassette Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Customizable length copper line set with flare connections Energy-Star Certified AHRI Estimated Annual Operating Costs: Cooling: $70.00 Heating: $231.00 [[SERIES]] What's Included Indoor Unit Outdoor Unit Panel Wireless Remote Control Various Installation Kit Options Available Flare Connection Leak Guard Sealer Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 year compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 110~120V, 60Hz, 1Ph Cooling Rated Capacity: 12,000 BTU/h Cooling Capacity Range: 4,200~17,000 BTU/h Cooling SEER: 21.5 BTU/w Heating Rated Capacity: 12,000 BTU/h Heating Capacity Range: 4,300~17,100 BTU/h Heating HSPF: 10.5 BTU/w Refrigerant Type: R410a Suitable Area: 350~450 Sq.F Indoor Unit Data Model: CB012GMFILCFHD Air Flow (Hi/Med/Lo): 379 / 309 / 261 CFM Sound Level (Hi/Med/Lo): 43.0 / 39.0 / 36.0 dB(A) Net Dimensions (WDH): 22.5 x 22.5 x 10.3 Inches Carton Dimensions (WDH): 25.8 x 25.8 x 11.5 Inches Net / Gross Weight: 35 / 41 Lbs Panel Data Net Dimensions (WDH): 25.5 x 25.5 x 2.0 Inches Carton Dimensions (WDH): 28.0 x 28.0 x 5.0 Inches Net / Gross Weight: 6 / 10 Lbs Outdoor Unit Data Model: YN012AMFI22RPD Sound Level: 57.5 dB(A) Net Dimensions (WDH): 31.5 x 13.2 x 21.7 Inches Carton Dimensions (WDH): 36.2 x 15.4 x 24.3 Inches Net / Gross Weight: 81 / 88 Lbs Manuals & Downloads Series Technical Brochure Series User Manual Series Installation Manual Series Service Manual Series Disassembly Guide AHRI Certificate Energy Guide


Pioneer® 18,000 BTU 20.5 SEER2 8-Way Compact Cassette Mini-Split Air Conditioner Heat Pump System Full Set 230V - 10 Ft

Overview Summary Ultra High Efficiency Inverter++ ceiling cassette split heat pump system Cooling capacity: 16,000 BTU/H with 20.5 SEER2 / 12.5 EER2 efficiency Heating capacity: 19,000 BTU/H with 10.5 HSPF2 / 2.78 COP2 efficiency Voltage: 208~230 V, 60 Hertz, 1 Ph Ceiling Compact Cassette Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Customizable length copper line set with flare connections Energy-Star Certified AHRI Estimated Annual Operating Costs: Cooling: $103.00 Heating: $356.00 [[SERIES]] What's Included Indoor Unit Outdoor Unit Panel Wireless Remote Control Various Installation Kit Options Available Flare Connection Leak Guard Sealer Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 year compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 16,000 BTU/h Cooling Capacity Range: 5,600~16,000 BTU/h Cooling SEER2: 20.5 BTU/W.h Cooling EER2: 12.5 BTU/W.h Heating Rated Capacity: 19,000 BTU/h Heating Capacity Range: 7,700~19,000 BTU/h Heating HSPF2: 10.5 BTU/W.h Refrigerant Type: R410a Suitable Area: 400~650 Sq.F Indoor Unit Data Model: CB018GMFILCFHD Air Flow (Hi/Med/Lo): 365 / 310 / 265 CFM Sound Level (Hi/Med/Lo): 43.0 / 38.5 / 34.5 dB(A) Net Dimensions (WDH): 22.5 x 22.5 x 10.3 Inches Carton Dimensions (WDH): 25.8 x 25.8 x 11.5 Inches Net / Gross Weight: 35.7 / 47 Lbs Panel Data Net Dimensions (WDH): 25.5 x 25.5 x 2.0 Inches Carton Dimensions (WDH): 28.0 x 28.0 x 5.0 Inches Net / Gross Weight: 5.5 / 9.9 Lbs Outdoor Unit Data Model: YN018GMFI22RPE Sound Level: 59.0 dB(A) Net Dimensions (WDH): 35.0 x 13.5 x 26.5 Inches Carton Dimensions (WDH): 39.2 x 15.6 x 29.2 Inches Net / Gross Weight: 94.4 / 101 Lbs Breaker Needed: 20A (double-pole) Manuals & Downloads Series Technical Brochure Series User Manual Series Installation Manual Series Service Manual Series Disassembly Guide CYB018GMFILCAD Submittal Sheet AHRI Certificate Energy Guide


Pioneer® 24,000 BTU 21.5 SEER2 8-Way Slim Cassette Mini-Split Air Conditioner Heat Pump System Full Set 230V - 50 Ft

Overview Summary Ultra High Efficiency Inverter++ ceiling cassette split heat pump system Cooling capacity: 24,000 BTU/H with 21.5 SEER2 / 12.5 EER2 efficiency Heating capacity: 25,000 BTU/H with 9.7 HSPF2 / 3.32 COP2 efficiency Voltage: 208~230 V, 60 Hertz, 1 Ph Ceiling Compact Cassette Air Conditioning & Heating System Variable Speed DC Inverter Operation Mode Customizable length copper line set with flare connections Energy-Star Certified AHRI Estimated Annual Operating Costs: Cooling: $153.00 Heating: $503.00 [[SERIES]] What's Included Indoor Unit Outdoor Unit Panel Wireless Remote Control Various Installation Kit Options Available Flare Connection Leak Guard Sealer Installation Manual User’s Manual Manufacturer Warranty Our Guarantee 5 year parts limited warranty 5 year compressor limited warranty Features [[FEATURES]] Technical Information Certifications Performance Data Power Supply: 208~230V, 60Hz, 1Ph Cooling Rated Capacity: 24,000 BTU/h Cooling Capacity Range: 8,100~26,200 BTU/h Cooling SEER2: 21.5 BTU /W.h Cooling EER2: 12.5 BTU/W.h Heating Rated Capacity: 25,000 BTU/h Heating Capacity Range: 10,600~30,000 BTU/h Heating HSPF2: 9.7 BTU/W.h Heating C.O.P.2: 3.37 W/W Refrigerant Type: R410a Suitable Area: 600~950 Sq.F Indoor Unit Data Model: CB024GMFILDFHE Air Flow (Hi/Med/Lo): 706 / 635 / 547 CFM Sound Level (Hi/Med/Lo): 49.0 / 46.0 / 43.0 dB(A) Net Dimensions (WDH): 32.6 x 32.6 x 8.2 Inches Carton Dimensions (WDH): 35.8 x 35.8 x 9.8 Inches Net / Gross Weight: 47.2 / 55.3 Lbs Panel Data Net Dimensions (WDH): 37.7 x 37.7 x 2.2 Inches Carton Dimensions (WDH): 40.8 x 40.8 x 3.5 Inches Net / Gross Weight: 13.2 / 19.8 Lbs Outdoor Unit Data Model: YN024GMFI22RPE Breaker Needed: 25A (double-pole) Sound Level: 61.0 dB(A) Net Dimensions (WDH): 37.2 x 16.2 x 31.8 Inches Carton Dimensions (WDH): 42.8 x 19.6 x 34.0 Inches Net / Gross Weight: 124.8 / 134.9 Lbs Manuals & Downloads Series Technical Brochure Series User Manual Series Installation Manual Series Service Manual CYB024GMFILCBD Submittal Sheet AHRI Certificate Energy Guide


Pioneer® 24,000 BTU 21.5 SEER2 8-Way Slim Cassette Mini-Split Air Conditioner Heat Pump System Full Set 230V - WITHOUT INSTALLATION KIT